HVAC Contractors and Plumbers in Carmichael, CA
In need of plumbing or HVAC services in Carmichael, CA? Consider working with Crystal Blue Plumbing, Heating & Air. We offer fast and reliable services 24 hours a day and are committed to complete customer satisfaction. Our motto is “Customer service the way it used to be!”
We’re proud to serve Carmichael for any home service needs including:
We Serve The Following Zip Codes in Carmichael, CA:
95608, 95609, 95841
See what Carmichael residents have to say about working with us below:
for Carmichael, CA
Diana - Carmichael, CA
David - Carmichael, CA
Very knowledgeable and efficient .
Quick response with excellant services
Joe - Carmichael, CA
Excellent service - the technician went up and beyond.
Virginia - Carmichael, CA
Very satisfied with his work.
Kevin Was Great
James - Carmichael, CA
I had a very positive experience with Crystal Blue Plumbing, specifically with Kevin the plumber. I called in the middle of the afternoon and he was onsite within 2 hours. He was quick and efficient, spending only about an hour to resolve my plumbing issue. I'll definitely call these guys again if needed.
some who cared
ruthie - Carmichael, CA
I was having toilet issues and 2 plumbers had already came out the last 2 days and said they fixed it. The toilets functioned for less then a few hours before I had to call another plumber. The 3rd plumber (and 3rd plumbing company) from Crystal Blue ran a camera in the line and cleared out the roots and then double checked to make sure he actually fixed the problem. He even came out on Saturday evening. I'd give Crystal Blue and the plumber 10 stars if i could!!!!
Shawn - Carmichael, CA
Technician was prompt and did a fantastic job. I have worked with many contract plumbers befor so I was ready for an over inflated price, at which time I would turn him away, however his quote was fair and the workmanship was quality. He took the time to explain the problem and explore solutions with me and was over all very professional and knowledgable. I would highly recommend this company. They also managed to fit me in on same day service!
Performed ac diagnostic on 26 yr split system attic. Found system not turning on the fan. Ac condenser comes on but no fan, tested fan by itself and with heat, nothing. Checked blower capacitor 12.5@10 out of range but not by much. Found that control board isnâ€™t producing power to turn on blower. Took control board off of unit and found what looks to be a burnt and broken soldier point. See pictures.Replacement of primary control board. Disconnected power to unit, removed old board installed new board per manufactures specifications. And then tested system. System cooling when I plugged system in to test. System working well for now.Keep an eye on blower capacitor and blower has slight vibration.House cooled from 83-81 degrees.
Carmichael ca Completed plumbing maintenance, water heater is a five-year-old GE 38 gallon gas located in the garage, it has no expansion tank, incorrect earthquake straps, and no gas dirt leg. Water pressure to the house is 60 PSI, master bathroom right hand sink pop up assembly is partially disassembled and the Hall bath toilet needs a new fill valve
Finished gas line, pressured line up to 15 psi found no leaks, capped off existing gas line tested everything is working properly homeowner is satisfied
Run auger through toilet to unclog Ran auger through toilet a couple different times to clear, did not pull back any debris, unknown blockage. Flushed toilet severel times, toilet is running/operating fine.
Talked to tenets about issues with toilet. (when toilet is flushed first time of the day no problems. if toilet is used within another 4 to 5 hours and/or toilet flushed more than more than once in combination of handwashing sink in the same bathroom water pipes begin to back up this is caused by two conditions restriction in pipe not allowing system to drain properly to a wet vent. or air vent for this sewer line is plugged. (possible causes of vent being plugged. vent going to roof is restricted due to possible material back flowing from previous restriction, plug in air vent and or stuff plug-in air vents from top birds, rats dropping stuff down air vent, leaves. Vent has been disconnected due to possible remodels that were done above disconnection sewer line from vent.) it is possible both issues are occurring at the same time due to information that I have gotten from tenets at first it couldâ€™ve just been a restriction in line but due to the current condition it appears the v
Install Navien tankless npe 210s with 60 ft of 1 inch gas line, new venting, expansion tank, isolation valves, condensate line, t and p line, removal and disposal of the old water heater. This unit has a comfort pump. This will be placed in the garage and will come with warranty and 1 yr service plan that includes a tankless flush. We are returning within the next couple days to address issues with the new gas line the system is temporarily being ran off the exaisting half-inch line everything is working
Main line tie in needs corrections also needs a test tee so line can be properly tested for inspection currently thereâ€™s a combo and fernco fittings with the offset a 4 inch wye would be a better solution to resolve this issue. Minor excavation required To install new fittings. Rough in height for laundry box is not correct needs to be 42 inches from the floor. Made corrections to main line tie in installed service tee so test ball could be inserted to fill line properly filled line above ceiling height no leaks everything is holding jimmy can call for reinspection
Called customer at 8:30 to inform her nuthatch I was on my way. Customer stated that she tried to contact the office multiple times yesterday to reschedule appointment and also this morning before she left for work. Customer would like a call back Monday morning to reschedule appointment.
Due to the windows on the side of the house and not having proper clearances the only way an outside unit would be able to fit would have to be right above the ground because of this I donâ€™t recommend the unit be put there #no we are Returning Monday to install a Navion tankless
Customer is going to call shop to sch job
Customer will get back to us once owner is notified
No answer.. left a voicemail at 11:30
Recommend to install a new navien tankless water heater with gas line, isolation valve, ball valves ,venting, electric outlet, permit and removal of the old unit#no I will be calling Terri tomorrow
Provided estimate for approval Talked to office lady someone has attempted to fix leak toilet has not been used in several months we would need to pull toilet and camera line inspect flange to determine where leak is coming from also the toilet seat is broken causing hazard recommmend replacing that repair costs will be determined once leak is found.
Performed ac diagnostic Carmichael. Found failed hard start kit, Need to replace the failed part, and recommend replacing dual capacitor as well because it is out of specs. Signed up on annual maintenance plan to help lengthen life of system. Added refrigerant caps, and reinsulated lineset to unit.
Customer stated that water and drain for dishwasher not connected, upon arrival dishwasher had water and drain connected. No issue, no charge to customer.
Front living room area is warmer then rest of house due to heat load new system would not take care of that problem. needs additional ductwork to counteract heat load due to vaulted ceilingâ€˜s and low insulation. Provided estimate to customer for additional ductwork and whole house fan
Duct work past airflow and duct seal good found no locking caps and missing brass caps customer found and picked up and put in garage install brass caps and installed new locking caps brass caps
Performed diagnostic on ac Carmichael, 7 yr old American standard rooftop condenser on metal tile roof. found inside working rooftop unit not working. Found bad dual capacitor. Tested unit, high start amps recommend hard start kit. Changed filter for client. Also recommend annual maintenance on system to prevent these kind of break downs.Set for plumber to come out and look at what it takes to connect the dishwasher drain 8-1-19. 8-10 in the morning.
Talked to client over phone, system tripped breaker. She reset it and changed batteries in tstat and hasnâ€™t happened again. Also had her look at breaker said it was 50 amp, so it might be a week breaker... if the problem happens again she will call in and schedule an apt.
Performed ac diagnostic York rooftop package unit. Found system running on arrival then while I was in front of unit it tripped. Checked the fuses in the disconnect max fuse size 35, and they are 35 amp fuses. Ok. Then checked and tightened all power wires and went to go look at breaker panel. found 40 amp double pole Zinsco skinny breaker. Missing the bar between the legs of power. When I pulled the panel found a wasp nest inside of unit.Need to remove wasp nest to test system, and test breaker more. Clients boyfriend helped me remove wasps. Then checked and tightened connections.Went back up on roof and tested system, running at 10 amps nowhere near enough to trip breaker. So my conclusion would be wasps kept tripping it.If problem happens again recommend replacing breaker with new Zinsco skinny 2 pole 40amp.
Called number listed couldnâ€™t get through to anybody left message, will try again tomorrow morning.
Performed ac tune up Carmichael. 12 yr old rooftop package heat pump unit pretty dirty, need to give whole unit good bath. Coils and panels. Found drain lines not attached again this time I recommend we properly glue everything back together. Found dual capacitor out of range. And system doesnâ€™t have hard start kit. Refrigerant pressures ok. Washed electrostatic filter. Duct work silver flex attic.Re attach drain line correctly, so it doesnâ€™t keep falling off. See picture. Dual capacitor changed out 45-5. And installed system with hard start kit or compressor saver kit to help lengthen life of system
Performed ac maintenance Carmichael, 14 year split trane system upstairs closet side yard. washed and cleaned condenser. Found system has too many filters in it. Only want 1 filter at unit. Tested refrigerant ok. Capacitor low 50@46. Below manufactures recommend replace. Contactor looks good. Electrical looks good.Emailed quotes for filter, capacitor, and membership. As well as the ac tune up today.
Remove old equipment per EPA regulations and install Trane 3 Ton 16 SEER single stage condenser and Coil matched with Trane 80% Up flow constant torque blower motor, gas furnace with new filter rack. Condensation pump needed. New Basic programmable thermostat. All work is performed with permits and title 24 duct testing