Fair Oaks, CA
HVAC Contractors and Plumbers in Fair Oaks, CA
It shouldn’t be a hassle to locate an excellent plumber or hire a skilled HVAC contractor for your home or commercial building. In fact, all you have to do is call Crystal Blue Plumbing, Heating & Air. We’re a licensed and insured plumbing and HVAC company serving Fair Oaks, CA. We’ve been in business since 1976 and focus on seeing that all our customers receive “Customer Service the Way It Used to Be!”
We provide Fair Oaks with the best in home services including:
- Plumbing Repair and Install
- Professional Water Heater Plumber Services
- Drain Clearing & Rooter Services
- Air Conditioning Repair & Replacement
- Heating Replacement, Maintenance, & Repair
Plus we provide 24–hour emergency service and free estimates!
We Serve The Following Zip Codes in Fair Oaks, CA:
Have Plumbing Needs? Our Plumbers Are the People to Call!
Even a small home contains a complex plumbing system that must receive work from licensed professional plumbers from time to time. This isn’t a field for amateurs! To ensure your plumbing receives the best service from plumbers who care, contact Crystal Blue Plumbing, Heating & Air. We work with sewer lines, septic tanks, water lines, bathroom and kitchen plumbing, sump pumps, leak detection, and anything else you may need for a healthy and helpful plumbing system. We’re ready to help you 24 hours a day, 7 days a week.
for Fair Oaks, CA
Morris - Fair Oaks, CA
Larry does Good job and is very friendly
Chuck - Fair Oaks, CA
Kevin was On Time, Professional and AWESOME!!! He did a great job identifying and fixing the problem quickly and professionally.
Responded quickly on a Saturday to clogged kitchen drain
Dave - Fair Oaks, CA
Very thorough, stayed with agreed cost even though project took much longer initially expected. Very courteous. I will use again, and recommend Crystal Blue!
Hard working, excellent people skills, quality job!
sheila - Fair Oaks, CA
What a great job! Tom and his crew were very pleasant to work with and took the time to fully understand the problem we had with an outdoor drain. They were thorough and cleaned up after solving the problem. I'd recommend Crystal blue Plumbing any time.
gustavo - Fair Oaks, CA
We will remove both systems per EPA regulations and two 5 Ton gas/electric package units with fresh air economizers per commercial code are required to have these fresh air economizers to be able to pull in fresh air into dwelling on demand. Both units will be the brand of Day and Night units. This brand of equipment will allow direct connection to original roof curb due the dimensions being the same as old units. We then will connect and seal unit to original curb and weather seal around perimeter. Install economizers to both units as these are separate pieces of equipment that need to be installed to meet commercial code. We will then install all new electrical 3 Phase disconnect and all new gas connectors such as gas flex sediment trap. A crane will be needed to remove old equipment safely and hoist new equipment into place. All proper permits and testing will be pulled and performed.
This is for 4 package units on the roof and a quarterly service plan. 2 newer package units and 2 older ones. Will be giving estimate for replacement of 1 and 2 rooftop package units. These units take Filters 16-25-2 x2 for each system so when servicing need 8 filters.
Performed a whole home plumbing inspection, found both lavatory faucets had not hot water pressure. The expansion tank assembly was built in galvanized piping, hall bathroom angle-stops did not work. Hose bibb in the front yard was not working, discussed said issues with the customer. Master bathroom I installed a new cartridge, hall bathroom could not find the cartridges so I installed a new Price Pfister widespread faucet. Installed a new hose bibb in the front yard, and replaced both angle-stops in the hall bathroom with quarter turn ones. Turned the water on and tested everything with no leaks and full pressure at all the fixtures.
Performed annual heating maintenance fair oaks. 12 yr old York split upflow closet. Tested system, system operational. Went thru system safety features. Ok at this time. Checked blower and motor, dirty. Cleaned motor fins. Blower capacitor firstname.lastname@example.org ok. Hot surface ignitor @70ohms. Cleaned burners and flame sensor. Took Video to show how ignitor works. Noticed the plenum of the unit is not fully sealed, see pictures. Recommend sealing the plenum. And thinking about adding a dedicated surge protector to your equipment.
We were out a few months back to clear the line. Line appears to be stopping up again. Various options for clearing line...recommend more thorough services like Jetter service
-Remove existing combination shut off - Remove currently installed combination valve to dishwasher - Install new shut off valve for cold water shut off - Test by operating valve repeatedly
Hall bathroom toilet leaking from base. Will pull toilet and remove old faulty wax ring and install new wax ring seal and re-seat toilet. Once toilet is set, will reconnect water supply line and test for leaks.Returned on Monday October 14 to remove and reset toilet per estimate. Found bad wax ring and tile floor to be uneven. Toilet did not have shims to accommodate for uneven floor. As a result toilet flange is not even to finished floor. Installed flanged wax ring and wax ring extender to accommodate toilet flange. Once toilet was set installed three shims at biggest gaps from floor to toilet to accommodate uneven floor. Tested toilet multiple times for leaks, no leaks, and put silicone around base of toilet per code.
Connect self supplied equipment. 4 total air handlers And to install the line said to each air handler. Line set covers will be homeowners responsibility to purchase it if you want the line set to be covered. Cannot guarantee system warrantyâ€™s due to it being self supplied equipment. If you didnâ€™t does not start up, it is not our companyâ€™s responsibility to replace equipment. Must sign a waiver if you want us to do the work. If more material is needed, you will be responsible to purchase it as needed.This cost is to install the air handlers only and start up equipment. This cost includes our labor.
Customer, owner, Beth declined work at this time stating that she wanted to get another quote for repair on hall bath toilet. Customer stated that our quote sounded like too much. Customer will call if in need of our services to schedule new appointment.
Install 3 head mini Split. (2) 9k air handlers Ceiling cassettes with (1) 12k Ceiling cassette. (1) condenser outside. All Refrigerant lines and electrical runs are included in this proposal. Each room will have individual control (true zoning) all work will be done to manufacture specifications and run tested on each mode. Permits and Title 24 will be homeowner responsibility per her request.
Homeowner is looking to change her garage into a laundry room with a secondary kitchen and bathroom. She is needing estimate to run sewer lines and water lines, To complete this we would have to find the main sewer pipe use the locator to determine death dig up from the yard to the garage dig under the garage, cut up in concrete to run new waist line to the laundry, kitchen, bathroom. Unable to give proper estimate not sure with death that the sewer line is, I left an estimate to have our sewer technician come out and run a camera use the locator to determine depth so we can make sure the proper grade is available. #no homeowner is going to call 811 dig first and see if they will locate the depth
Remove old Split system Heat Pump and install 2.5 Ton 14 SEER American Standard Heat Pump. To install new unit in ceiling area we will have to remove sections of T-bar ceiling this will require some paint damage you may have to repaint after job is completed. installation of new air handler will use existing drain pan, existing supports, existing Plenums. will reattach new equipment to existing material will use new parts as needed. installation of condensing unit on roof with support and strap condenser to roof supports. will install separate stand for service disconnect cannot be attached to unit per code anymore. will install new electrical from service disconnect to unit. will reconnect existing low-voltage wiring. will reconnect existing lines. will pressure test, vacuum Noncondensibles out of system and charge system to manufacturers recommendations.
#no. Remove old Split system Heat Pump and install 2.5 Ton 14 SEER American Standard Heat Pump. To install new unit in ceiling area we will have to remove sections of T-bar ceiling this will require some paint damage you may have to repaint after job is completed. installation of new air handler will use existing drain pan, existing supports, existing Plenums. will reattach new equipment to existing material will use new parts as needed. installation of condensing unit on roof with support and strap condenser to roof supports. will install separate stand for service disconnect cannot be attached to unit per code anymore. will install new electrical from service disconnect to unit. will reconnect existing low-voltage wiring. will reconnect existing lines. will pressure test, vacuum Noncondensibles out of system and charge system to manufacturers recommendations.
Performed ac diagnostic 12 yr old heat pump. Found inside air handler running and not cooling air. Found system has lost refrigerant again. The system has sprung a refrigerant leak. See picture system is flat. Due to its age and the type of refrigerant recommend looking into replacement over repairs.We have taken care of each issue as it has come first visit the thermostat didnâ€™t work, then the system kept leaking water due to refrigerant charge was low, then the parts went bed. Now it is flat again. All over 2 months.Ken to come out tomorrow for replacement pricing
Performed ac diagnostic Fair Oaks. On a 12 yr trane split heat pump. Found bad dual capacitor causing unit not to turn on, also recommend replacing hard start kit, out of range. Also found ac power had blown a fuse. And that was most likely due to the wasps that built there nest inside the unit.Challenge is breaker panel is blocked by shelves, tried to reset breaker multiple times finally got it to flipTested system after installing new dual capacitor, new hard start kit, and 1 new fuse. Also tried to close holes in disconnect to stop wasps from coming back.
Access undersink will run 100 machine to clear out blockage.cleared line tested good.
Performed diagnostic fair oak, 12 yr split York, found inside unit turning on and outside compressor turning on but outside fan not running. Tested dual capacitor, found bad. Replace dual capacitor since itâ€™s dead, and tested system. System running ok at this timeWith yearly maintenance plan 1 AC tune up, 1 furnace tune up, and a plumbing inspectionSwitching to a permanent washable filter from the disposable ones. Save you money over the life of the system. Especially when changing filters more frequently.
Customer complained about brown water coming through faucet for bathroom tub/shower fixtures. Ran water in downstairs guest bathroom tub, water ran for a couple of minutes before turning color. Looked at water heater in garage. Found 13 year old water heater that has never been serviced. Water heater is also leaking from base. Water heater needs to be replaced. Gave customer quote for installing standard and tankless water heaters. Existing water heater can not be flushed given its age, and that it is already leaking. Flushing water heater will cause more issues. Water heater also has signs of flame roll out indicating that gas chamber is no longer sealed properly. Customer is getting multiple quotes for insurance to replace under home warranty.
Fair oaks customer stated gust bathroom tub to be slow to drain. Upon arrival found that tub stopper was tripped halfway. Tested tub by running tub spout and shower for several minutes, tub is not backing up or slow to drain confirmed water flow at main line clean out in back of home. Informed home owner of crystal blue membership, owner is going to review brochure and get back to us. No issues at this time, no charge to customer.
Called phone numbers on file to get approval to start work but was unable to get anybody on the phone to get the approval
Found system still leaking out secondary above cabinet.After getting system working found system low on r22 refrigerant. Need to charge system to prevent leaking of condensation. Charged system to get unit above freezing point of refrigerant, see pictures.Also checked drain lines to verify draining correctly, cleaned up around drain.Emailed commercial maintenance plan info to client
Went thru and found what system is yours since nothing on roof is labeled. Found roof top unit has power, and refrigerant, but canâ€™t tell if anything else is going on till we install a new working thermostat.Replaced thermostat and tested system. Found system possibly low on r22 refrigerant, that explains the water in secondary pan, if water keeps leaking will need to charge system. System on and working at this timeEmailed commercial hvac plans to clients
Kohler piston drive is coming apart at the fill tube for bowl and the fill valve that delivers water to tank is bad will replace both parts. Size of tank is 1.5 gallons installed new piston and fill valve tested good
Because pipes are older I highly recommend adding two cleanout at picture, I located line and cleanout would be installed in plant area approximately 3 feet deep and is harder access