HVAC Contractors and Plumbers in Folsom, CA
If you demand more from your professional HVAC contractor or plumber than simply “repairs today,” then Crystal Blue Plumbing, Heating & Air is the company to call. We’ve been in business since 1976 and are fully licensed and insured. We are committed to making each customer a customer for life with exceptional service–that’s why our motto is “Customer Service the Way It Used to Be!”. We’ve been serving Folsom and the surrounding area for over 40 years, so we’ve seen it all.
We provide Folsom with the best in home services including:
- Plumbing Repair Services
- Water Heater Replacement & Installation
- Rooter & Drain Clearing
- AC Maintenance & Installation
- Heating Installation & Maintenance
We offer free estimates and 24–hour service.
We Serve The Following Zip Codes in Folsom, CA:
Our Plumbers Can See That Your Plumbing Is in Top Shape
“The best thing since indoor plumbing…” That’s a comparison used for many beneficial inventions. But indoor plumbing can become a major problem if it isn’t treated well–and that requires the work of licensed professional plumbers. Allowing amateurs to tamper with your home’s plumbing can lead to leaks, building damage, and water waste. To have any plumbing work done right the first time, put your trust in Crystal Blue Plumbing, Heating & Air. Our services cover everything from leaky faucets to work on septic tanks and sewer lines.
for Folsom, CA
Sara - Folsom, CA
Very Professional and knowledgeable
Steven - Folsom, CA
Grayson was knowledgeable, thorough, kind and willing to work with us.
Crystal Blue Plumbing and Grayson
Steven - Folsom, CA
Crystal Blue Plumbing was professional and very thorough throughout the start of our situation. Grayson was knowledgeable and took his time in assessing our issues.
Gloria - Folsom, CA
We were very satisfied with our routine maintenance today..he was professional and courteous. ..thank you for being great company.
Keiton changed filters
Melinda - Folsom, CA
Second time dealing with keiton & always polite & professional.
Melinda - Folsom, CA
The two young men who serviced our air conditioning system was very polite & professional.
New System Estimate
Janice - Folsom, CA
Very professional, personable and answered my questions. Provided instant estimate to install new air conditioner and followed up quickly with written estimate.
Gloria - Folsom, CA
Samuel was wonderful and we learned alot..He was friendly and professional. .a pleasure to meet an asset to your business
Jesse - Folsom, CA
Awesome service! Very professional & experienced.
Melinda - Folsom, CA
Scott was amazing! Very personable, professional & experienced. Amazing service!
Charging system back to designed levels of refrigerant. This includes weighing out exactly how much refrigerant I put into system. NOTE IF SYSTEM LEAKS MORE THAN 15% ANNUALLY WE CANNOT LEGALLY CHARGE SYSTEM AGAIN.No guarantees on how long the refrigerant will last. Need to locate where it is leaking if refrigerant does not meet the 15% annually leakage allowance.Charged system and weighed in 6.295lbs of refrigerant. System which is on a piston metering device and Iâ€™m showing 25 degrees superheat which is In range and cooling well. Pressures are 76psi Lowside and 241 psi Highside. Indoor vent temperature is showing between 58-60 degrees and indoor ambient temperature at 82 degrees.
Shut water off to existing toilet Remove existing faulty toilet flush valve Dispose of existing flush valve and prep toilet for new Modified toilet spud to create watertight seal between toilet and flush valve Flush valve cut to fit and installed according to manufacturer specifications New flush valve tested for leaks using building pressure and flushing repeatedly Start up sequence and fine tuning included 90 Day WarrantyCustomer not available for payment crystal blue plumbing will contact at later date to collect
Reconnect all condensate drains into correct pipes. So that secondary only drains above window and primary drains near ground. Includes adding â€œPâ€ trap in proper location as well as a clean out for primary and secondary.
Performed ac diagnostic Folsom. Found 26 yr old split system ac not running. Found compressor capacitor dead. replaced capacitor and tested system. Refrigerant pressures ok at this time, filter 14-24-1 due to be changed.Signed up for Annual membership. Which includes ac tune up, furnace tune up and plumbing inspection. Plus priority service and a 10% discount. Good for 1 yr.
Replaced control board for downstairs unit, and tested system. System operational at this time. Ac running on departure.
Out to clear primary drain line. Secondary drain line is dripping above window and pan has water in it. Consists of clearing clog in primary drain line in attic. Blowing compressed nitrogen through line to remove debris.Company who installed system plumbed in the Primary, Secondary, and drain pan into secondary drain coming out above window.WANTS RECEIPTS MAILED TO HER IN PAPER
Performed ac diagnostic, found downstairs split system running indoor fan/ not running outside, Contactor not closing. need to look into low voltage wiring.York diamond 80 furnace low voltage terminal on primary control board, has cracked connections. See picturesGot system running today no gaurentee it will last.Got control board on will call. At us air
Performed diagnostic in Folsom. Unit a running and operating but unit is not cooling. System runs on r22 refrigerant and is very low on refrigerant. Showing 18psi Lowside and 160psi Highside. Will need to add refrigerant and inject fluorescent dye into system. Informed homeowner that system is getting old and repairs may end up costing the same as a new system would. Informed him that i would send out a comfort advisor to quote him on a new system.Compressor runs on and turns off frequently due to very low refrigerant levels.
Replace vent condenser fan on Goodman condenser. The unit is shaking aggressively and the fan is hitting the copper inside the unit. Fan blade has a small bend in it causing unit to shake. This includes replacing condenser fan with brand new balanced one. If the fan blade has been out of alignment for too long it couldâ€™ve worn the bearings in the motor and then motor would need to be replaced as well.Did repair on Goodman condenser on side of house. Disassembled top of condenser to gain access to fan blade. Oiled new fan blade so shaft does not rust onto new fan blade. Tested system to ensure that the shaking has subsided. System operating quietly and no more shaking.Checked refrigerant levels today because I was unable to due to shaking of unit. Refrigerant levels are showing for R22 64 psi Lowside and 207 psi Highside and is where it should be.
For this estimate we would be replacing the shower trim set and tub drain ring. In order to change out the shower trims including the mixing valve we will have to shut down the water to the home, remove all old trim and make A cut into the drywall on the other side of the shower in order to cut out and remove the old mixing valve and soldering new mixing valve. Before closing the wall we will turn the water back on and test for leaks. After seeing everything working properly And having no leaks we will then put drywall back with mud and tape. Then finish installing trim using caulking anywhere it may be necessary.
Customer has a 10+ year old tankless water heater that has stopped working, upon diagnosis cleaned the water filter screen. Called Norritz tech support and determined the unit overheated and kicked an error bogging the unit down. I cleared the code and descaled the unit and even cleaned the burner hamper which was recommended by the manufacturer. Turned the gas and water back on and tested the unit multiple times and its working perfectly. We performed the descale for the membership but not the plumbing inspection.
Performed maintenance in Folsom. Unit is a Goodman condenser on side of house. Unit shakes violently and condensing coils are loose and shaking as well. Checked fam blade and is tight and blades are not bent or damaged upon visual inspection. Informed homeowner that to take unit apart further we would have to charge for diagnostic to further inspect why unit is operating badly. There is damage to copper line-set inside of unit. Will need to send out senior tech to diagnose issue.Checked capacitor and is rated for 60/5uf +-6% and is showing 65.1/4.9 and is about 1% out of range on compressor side than manufacturer suggests is okay. All electrical connections and wiring are clean and not damaged or loose. Checked condition of contactor and is okay and working properly. Unable to checked for refrigerant levels as unit shakes so hard I donâ€™t want to damage homeowners unit.Will order and do repair once fan blade comes from goodman
Changed 13 supply and 2 return ducts with r8 silver flex ducting. Strapped ducts in attic per code standards. Insulated exposed metal wyes. Pulled permit and scheduled title 24 testing for client. Removed old thermostat, found thermostat wire has 6 colors. Used standard 5 to hook up new digital WiFi nest thermostat for client. Installed nest app on clients phone. Went over how to use thermostat at actual thermostat and on the app in the phone. At package unit on roof installed new primary control board. Old one had burn marks/hot spots. Changed disconnect box, old one partially melted. Tested system, system cooling on departure. Cleaned up around house and attic.Due to us taking an extra day to get the job done, we will be providing a extra year of maintenance at no cost. So client will receive 2 ac tune ups, and 2 furnace tune ups, and 2 plumbing inspections, and his membership will be good till June 18 2022.
Performed annual ac maintenance, Lennox split system garage side yard. 7 yrs old. Changed thermostat for client. Washed filter. Checked system operation. System working at this time. Keep an eye on refrigerant levels. If they drop we will need to dye system, to see if thereâ€™s a leak.Resigned up for another year of maintenance
Went over a few options for customers shower trim sad and fixing his garbage disposal. Customer seems to be happy has the information he needs just have to talk with family member before making a decision.
Provided customer with three options ranging from 2600 down to 500 to make repairs including replacing cabinetry that has been damaged as a result of water leak customer will think about it and perhaps call us back in the future as she has multiple bathrooms available for use
Performed annual ac maintenance split system attic side yard. Attic looks good black flex ducts sealed. Drain pan dry ok. Outdoor fan motor has been changed, dual capacitor has been changed, and system has hard start kit. Tested system refrigerant ok for now, keep an eye on it for the future.
Returned to change filter for them, did not have correct size on truck. Filters changed 14*25*1 and 16*25*1
Performed diagnostic package unit roof. Found previous company has put both green and yellow together in wire nut. Control board has hot spots, will get system up and running correctly. What ever it takes to do that, will be changing control board, and thermostat. Client wants WiFi, likes nest.Also doing full duct replacement, pulling permit and title 24 testing.
Out for estimate for moving thermostat wires.
Out for estimate.
Performed annual ac visit, found reason system wasnâ€™t cooling as well as it should was, low refrigerant levels and dirty ac condenser coils. Cleaned coils with water bath and charged system with 1 lb r410a. If ever low again we will need to add up dye to system and recharge to find leak. Tested parts ok working for now. Not a fan of the kool kap it doesnâ€™t lift all the way messing with the refrigerant numbers.Charged system with 1 lb of R410a, refrigerant pressures improved. Keep an eye on refrigerant levels during future visits. Put kool kap to side of unit, needs to be put back on during the fall visit.
Performed a.c maintenance in Folsom. Unit is a Minisplit condenser on side of house. Coils are dusty and will need to be washed off. Checked all electrical connections and are okay no damaged wires or loose connections. Checked ductless minisplit filters and cleaned them and put back. Washed off coils on mini split condenser to improve efficiency and help unit cool better.Performed a.c maintenance in Folsom. This is for second unit at home. Unit is a Rheem condenser on back side of house. Unit is in good condition overall. Condensing coils are clean and free of debris. Checked all electrical connections and are okay showing no signs of wear and tear. Checked capacitor and is in range showing 45/5uf and is rated for 45/5uf +-6%. Checked refrigerant levels for R22 system and is okay showing 66psi Lowside and 289psi Highside. Overall system is working good and no issues identified. Unit is a Rheem Condenser MFG in 1998.
Performed ac diagnostic York split system, zoned. Down stairs unit thermostat lo batteries need to replace batteries, turned on upstairs unit. Outside not running. Electrical panel partially opened for condenser. Condenser coils falling apart.Dual capacitor dead, wonâ€™t know if that fixes problem until we replace part.Replaced dual capacitor, found breaker for ac off, turned on and plugged in unit. Running at this time. Let system run for a few mins and tested refrigerant.System is flat on refrigerant, see pictures. most likely from a leak in the outside coils where the dog peed on the unit. Unit holds a 9 lb charge of refrigerant. And as soon as we put it into the system it might leak right out again.Due to shape and age recommend replacement
Out for estimate, 4 ton gas electric package unit roof. May need service stand per new code. Also ducts grey ducts falling apart need to replace. See pictures.