HVAC Contractors and Plumbers in Folsom, CA
If you demand more from your professional HVAC contractor or plumber than simply “repairs today,” then Crystal Blue Plumbing, Heating & Air is the company to call. We’ve been in business since 1976 and are fully licensed and insured. We are committed to making each customer a customer for life with exceptional service–that’s why our motto is “Customer Service the Way It Used to Be!”. We’ve been serving Folsom and the surrounding area for over 40 years, so we’ve seen it all.
From air conditioning and heating repairs and drain cleaning to complete service for water heaters, you’ll find all your home or business needs in Folsom, CA with us. We offer free estimates and 24–hour service.
We Serve The Following Zip Codes in Folsom, CA:
Our Plumbers Can See That Your Plumbing Is in Top Shape
“The best thing since indoor plumbing…” That’s a comparison used for many beneficial inventions. But indoor plumbing can become a major problem if it isn’t treated well–and that requires the work of licensed professional plumbers. Allowing amateurs to tamper with your home’s plumbing can lead to leaks, building damage, and water waste. To have any plumbing work done right the first time, put your trust in Crystal Blue Plumbing, Heating & Air. Our services cover everything from leaky faucets to work on septic tanks and sewer lines.
for Folsom, CA
Melinda - Folsom, CA
Always impressed with all technicians
Jamal - Folsom, CA
Susan - Folsom, CA
Michael was efficient, professional and extremely good at what he does!
Bentley - Folsom, CA
Karen - Folsom, CA
Great service in an emergency!
Dana - Folsom, CA
Wicks - Folsom, CA
Jeff - Folsom, CA
Michael was very thurough with his estimates in two system options. It will help me make a more informed decision.
Job well done and at a fair price
Ken - Folsom, CA
Tom was very good and and got right on the job and took care of of the sewer line getting it cleared out.. Gave you up front information on what he was doing and also informed me of what might happen in the future. because I have a old sewer system. He is very polite and if needed I will call on Tom again.
frank - Folsom, CA
Professional and very knowledgeable ! Extremely efficient and finished the job in a timely manner.Everything was clean and back to normal when I returned home from work. Very trust worthy and will use Tom in the future for any and all plumbing and air conditioner needs.
Performed diagnostic Folsom. On a 10 yr heat pump 2 yr air handler. Need to figure out why unit is running fan after unit turns off per client. Need to catch problem with the fan running while It is happening. Could not duplicate problem today.Performed diagnostic, traced wires for zoned heat pump split system to see what could be causing problem. Problem must be intermittent. Can not duplicate.
Due to the age of expansion tank pin hole leak will replace and restore water to house.replaced tank turned on water everything tested good
Line draining slowly, Nitrogen purged line and blew the drain line out fully... pan drained and cleared. Dumped water thru the line to verify draining. Not sure if system being charged with r22 refrigerant and producing more condensation had anything to do with it... will need to nitrogen blast lines on our visits to be safe.
Folsom California AC heating maintenance performed AC maintenance for trane equipment upon arrival noticed suction line covered in oil which is typically an indication of a refrigerant leak. insulation missing from suction line as well. checked capacitors condenser fan capacitor 7.5 reads 7.0 compressor capacitor 70 reads 68.5 capacitor check is OK. fan reading just within manufacturers tolerance compressor capacitor check is good. manufacturers tolerance +/-6%. inspected electrical wire nuts tight contactor good electrical connections tight. inspected service disconnect found aluminum wiring coming from main house with no noalox (aluminum wiring protector anti-oxidize) it is used to protect the aluminum wiring from corrosion and becoming loose and overheating also found ground wire not connected. checked Lugnuts to verify electrical was tight found aluminum wiring connections not tight full turn and a half loose which is why the electrical wiring is already showing that the alum
Washed outdoor coils backside of condenser dirty., brushed filters off not that dirty system working well. Set up swing on remote.
Changed filters 16-25-1 is at top of stairs. 14-25-1 at bottom of stairs.Performed annual maintenance on 21 yr split heat pump. With refrigerant issues. It is either low on refrigerant, or has a bad metering device. Only way to tell for are would be to charge system above freezing point. Contactor looks ok, dual capacitor ok. Cleaned coils outside very dirtyAdded 1 lb of refrigerant, numbers got better above freezing for now but still appears to be a restriction/bad metering device. Will see if it holds.If not due to age of system 21 yrs and cost of repairs donâ€™t recommend repairs.
New cut in in Folsom for 1250 sqft home, single story. Install 2.5 Ton American Standard 15 SEER two stage gas valve, single stage cool with Variable Speed Blower package unit on roof, crane needed, adjustable roof curb needed. Run new gas line from meter thru attic to package unit. Run new electrical to panel, also install new electrical disconnect at unit. New flashing around adjustable curb to ensure that there is no leakage into home from rain. ( guaranteed for one year) Cut in all new R-8 Ductwork with all cans, connectors, yâ€™s and Title 24 seal to ensure no more than 5% leakage per code for new Ductwork. This job will include all permits along with 3rd party Title 24 Duct testing.///// Met with father, son was out of town. They will discuss later on in the week.
Was not water main cause meter was not spinning, I checked sump pump all working the sump pump was empty I illegally it up and water coming out of ground stayed the same. I customer just got back from vacation, and saw his grass was yellow, so heâ€™s been overwatering the grass and all ground water. Is flowing down hill, the grass is soaked. Told customer to stop watering for 3 days that should solve problem.
AC not cooling house below 80Â° diagnostic found system low on refrigerant second time in a month. last time out injected sealant into system. Performed system inspection to look for obvious leaks did not find any signs of leaking anywhere. while inspecting evap coil noticed bottom half of coil is iced over form being low on refrigerant and condensation drain pan full cleared restricted in drain line so condensation water in drain pan will drain. Found no obvious leaks 3 options for next step option 1 - injecte dye in the system and recharge system to allow dye to cycle through so leak can be found. This option will allow system to be used option 2 - refrigerant detection leak search pressurize system with nitrogen leaving refrigerant inside system this will allow meter to detect refrigerant additional pressure from the nitrogen will allow it to be found easier.Will go over every accessible part with the meter to detect the leak. This option will leave system usable until leak
Folsom California heating AC service heating AC maintenance heating AC diagnostic Ac unit not cooling below 80Â° Goodman ac condenser Visual inspection system restricted not able to get air througe bottom section of condenser coil. bark and dirt restricting airflow. as well as lattice work directly around unit causing system to recycle its own hot air as well as restricting the amount of air that can go through the condenser coil. This will cause condenser coil to run hotter putting more stress and wearing system out sooner then as designed. AC diagnostic found condenser coil plug restricting airflow causing high side refrigerant pressure to be higher than what it should be. after cleaning condenser coil retested refrigerant pressure. found pressure is indicating system is low on refrigerant.Charge system to manufacture specifications, installed sealant into systemPut lattice work back around unit recommendation is to remove it completely so system can breathe unrestricte
Exploratory break is under boulder and big roots
Sacramento California heating AC service heating AC maintenance heating AC diagnostic HVAC replacement. Performed AC maintenance - turned the unit on to check operation of system turned on / running with no problem. Checked refrigerant pressures good, checked amp draws compressor 17.3 reads 10.62 , outdoor fan 1.3 reads 1.07 , capacitors 45 /5 reads 43 / 5.1 capacitor good within manufacturers tolerance (+/- 6%) Visual inspection of electrical - wiring good no burnt or overheated wire connections, Service disconnect foond loose wiring connections tightened as part of AC maintenance, contactor - contact points slightly pitting and burnt not affecting function / normal wear. electrical megaohm test - unit passed / compressor tested caution this test indicates compressor windings starting to fail internally pretty normal with age of unit can expect to have to replace a compressor. performed simple water wash of condensing coil and flushed condensation drain line part of AC maint
New Expansion Tank, Flex Lines and Gate Valve
Replace kitchen sink pvc drain pipeline,itâ€™s ok right now but almost be leaking. All 3 toilet need new plastic and cut long screw. 2nd floor main both room right sink faucet already brokered has leaking,need replace new faucet with 1/2 inches by 3/8 inches hot and cold water supply lines,need fix Customer kitchen dishwasher doesnâ€™t drain ,need new air garp and clean the line ,the job included labor parts with one year warranty for new job labor only. Customer just bought a new washer dryer machine in second for all so we need to put a new drain pan the size about 30 by 32 inches ,the drain pan need connect to the drain line than put washer dryer on the pan and connect to the water valve .the job included drain pan with new job only.
Master bathroom shower doesnâ€™t have Enough hot water , need close main water for the house and take off shower hander make sure some stocked in there or cartridges has damaged. Checked toilet tank used old design boll fill valve ,lots leaking from the toilet tank ,need replace 3 toilet fill valve ,talked with customer,the toilet looks good .the job included labor parts with one year warranty for new job labor only. Customer want doing the job with shower cartridge in same day . Master bathroom shower cartridge doesnâ€™t have lots hot water ,already take off parts and doing the water pushers find lots small rock coming but the cartridge has damaged already so need replace new one. thatâ€™s 2 pcs special order ,need go find first than call customer and reschedule doing the job .the job included labor parts with one year warranty for new job labor only.recived $85 for checking today and included to this job cost .so the cost will be $597.85-$85
Master bathroom shower doesnâ€™t have Enough hot water , need close main water for the house and take off shower hander make sure some stocked in there or cartridges has damaged.
Folsom California heating ac service, heating ac maintenance, heating ac diagnostic, Performed ac maintenance. Visual inspection of electrical - no burnt or overheated wire connections. Found wiring for condenser fan motor and compressor rubbing against copper tubing caused by zip ties broke. wiring for condenser fan motor broken wire terminal protectors / casing. Fixed wiring part of AC maintenance. blower motor capacitor test at 10 good, Tested amp draws (good), condenser fan motor capacitor 7.5 test 4.9 bad ( allowable tolerance +/-6% )Recommend replacement to prevent stress / damage to condenser fan motor. Compressor capacitor 40 Reads 39.4 good, contact points good, Hardstart kit good, refrigerant pressure good, air filter clean, water washed condenser coil.Replaced condenser fan motor capacitor. System working found no other problems or recommendations needed at this time.
1 Laundry and kitchen need drain 2 water heater water supply lines need replace ,itâ€™s leaking. Laundry and kitchen drain.replace water heater supply line
Folsom California AC heating service AC heating maintenance AC heating diagnostic Goodman furnace not working Diagnostic - found hot surface igniter broken / cracked not igniting gas.Installed new igniter tested system found no other problems at this time.
Replacement of gas valve and control board. All part Replacements will have one year parts and labor warrantyFolsum California Ac heating service AC heating maintenance AC heating diagnostic Heating repair replace the gas valve and control board for trane gas package unit
Folsom California ac heating service ac heating diagnostic ac heating maintenance Residential and commercial HVAC service Diagnostic for heater not working no heat clicking noise. Found pilot light out on furnace. Lit pilot light tested furnace found no problems unsure why pilot light was out.
California ac heating service ac heating maintenance ac heating diagnostic heating diagnostic heater not working fan/blower intermittently speeding up and slowing down. Full diagnostic on system. system is operating properly at this time could not determine cause of the problem. flame sensor 2.5, tested pressure switches, tested variable speed motor, control board. all tested fine could not determine why blower motor was speeding up and slowing down.
Folsom California AC heating service AC heating maintenance AC heating diagnosticmain house heating maintenance. Visual inspection of electrical condenser (good) no burnt or overheated wire connections, A/H found burnt over heated wires for electrical heat strips and over heated electrical realy connection for electrical heat strips, capacitors condenser - 45/5 reads 42.6/5.2 testing low still within manufacturers tolerance by .3, Air handler - 10 reads 9.9 good, Tested amp draws (good), Tested defrost cycle (good), refrigerant pressures (good). filters cleanDuctless mini split heating maintenance inspection of electrical no burnt or overheated wire connections. found connections at outdoor unit main power loose tightened connections. also found wiring cut too short causing wires to be pinched in between metal lip and cover. this will eventually cause wires to short out and cause damage to unit. filters cleanReplaced realy and electrical connections in A/H per customers
Technician cleaned pop-up assembly and P-trap only drains great no machine needed minor clogged. Customer understands no warranty on drain clearing. Sinclair drains great customer happy. Complete plumbing inspection inside and out the house outside the house everything fine no leaks newer condition faucets Plumbing water heaters brand new. See recommendation for new pressure regulating valve valve at house Supply from meter measured 100 psi should only be 60 PS I highly recommend change out soon as possible to avoid any small line breakage including irrigation.
Folsom California AC heating service AC heating maintenance AC heating diagnosticPerformed heating maintenance. Visual inspection electrical good no burnt or overheated wire connections, blower motor capacitor test at 6 should be +\-6% of 7.5 test bad recommend replacement, Tested amp draws (good), Flame sensor reading 4.7 (good) Burners clean, Heater safeties good, Gas pressure 3.47 good, ohms reading of hot surface igniter 71.8 good. changed air filter. Visual inspection of ductwork good no broken or disconnected ducts. return duct attached to unit has a lot of tension due to installation of duct. This is causing inner liner of duct to come apart. System working at this time. recommended repairs - replace blower motor capacitor and replace / repair return duct. At this time customer has chosen to replace blower motor capacitor and will wait for return duct. New part has 1 year parts and labor warranty.