HVAC Contractors and Plumbers in Folsom, CA
If you demand more from your professional HVAC contractor or plumber than simply “repairs today,” then Crystal Blue Plumbing, Heating & Air is the company to call. We’ve been in business since 1976 and are fully licensed and insured. We are committed to making each customer a customer for life with exceptional service–that’s why our motto is “Customer Service the Way It Used to Be!”. We’ve been serving Folsom and the surrounding area for over 40 years, so we’ve seen it all.
We provide Folsom with the best in home services including:
- Plumbing Repair Services
- Water Heater Replacement & Installation
- Rooter & Drain Clearing
- AC Maintenance & Installation
- Heating Installation & Maintenance
We offer free estimates and 24–hour service.
We Serve The Following Zip Codes in Folsom, CA:
Our Plumbers Can See That Your Plumbing Is in Top Shape
“The best thing since indoor plumbing…” That’s a comparison used for many beneficial inventions. But indoor plumbing can become a major problem if it isn’t treated well–and that requires the work of licensed professional plumbers. Allowing amateurs to tamper with your home’s plumbing can lead to leaks, building damage, and water waste. To have any plumbing work done right the first time, put your trust in Crystal Blue Plumbing, Heating & Air. Our services cover everything from leaky faucets to work on septic tanks and sewer lines.
for Folsom, CA
Gloria - Folsom, CA
Scott is such a hard worker and very efficient at explaining things to us..he is kind and courteous and polite. ..we really like this young man..thanks for coming today..
Mary - Folsom, CA
we were pleased with scott.. he knew what he was doing and the job. got done fast. i would use him again. thank you for a good job.
Karen - Folsom, CA
Andreas - Folsom, CA
Ken provided a straight forward quote, answered all questions and delivered on time. We can finally enjoy our home comfortably whether it's very hot or cold outside
Mary - Folsom, CA
Bradford receives: Excellent!!! Over & beyond!!!
Knowledgeable Friendly and direct to points of concern.
Bill - Folsom, CA
Pricing was not in my budget range, but I appreciated the quote.
Karen - Folsom, CA
Knowledgeable, reliable, fast service.
Melinda - Folsom, CA
Always impressed with all technicians
Jamal - Folsom, CA
Susan - Folsom, CA
Customer wants a gas line installed for a future pool heater which is at 400K BTUâ€™s, gas meter is on the left front of the home. Pool heater will be installed on the back left side of the home, attic space is were the pipe would be ran. Upon exiting the left side of the home the gas line will be buried at about 15 feet over to where the heater will be installed. Gas piping size is at 2 inches to meet the BTUâ€™s and length of pipe, mega press fittings to save some time. Job will need 2 techs and up to 3 days worth of work, permit will be pulled and line properly inspected. Any code violations will be 100% handled and covered by our company, guaranteeing we do the job right the first time.
Found the repair The plumbing technician completed had faulty glue we redid the entire repair that we had done previously installed new PVC with a brand new can of glue. Tested and everything seems to be working
Water Line Patch Repair - Minor - Shut off water to whole house for repair - Cut and remove â€œrepair styleâ€ plastic tee - Remove corroded and broken valve to home for replacement - Modify piping to accommodate new water shut off valve - Install new heavy duty Schedule 40 PVC piping and fittings for extended durability - Test for leaks using city pressure - Customer verified plumbing operating correctly in home
Water repair needed - expose water line to repair - water line segment replacement - new water shutoff to replace corroded valve
Customer has a leak at his water main, he wants to use his home owners insurance.
Install new recirculation pump with timer and to 1/4 turn 1/2 inch ball valves and a 1/2 inch hose bib. Also install three-quarter check valve to stop the potential of hot water going into the cold water per Tim collect 660.00 in payment and the remainder in triad pr Tim
Performed furnace diagnostic. Found system has error code 5 flashes. Which is a blown low voltage fuse. Changed 5 amp fuse in co trip board and tested system. Found isssue with zone board wiring. Fixed and tested system. Heaters working cycled off each zone and then tested ac. System is on heat and running both zones on departure.
Performed ac diagnostic. On a 19 yr hydronics split system. Found system struggles to start. It started then I hooked up my gauges and found system is showing low refrigerant charge, so need to add refrigerant to see if itâ€™s the system being low on charge or if itâ€™s a bad metering device. Also I notice the unit isnâ€™t positioned correctly, the vertical clearance above unit should be 4 feet. This can be effecting the systems refrigeration pressures. As well as the back side of unit coils are dirty. This can be effecting refrigerant pressures as well.
Performed annual heating maintenance on a 8 yr Lennox split system, upflow garage Folsom. Tested system, system operating at this time. Cleaned combustion air vents. Brushed off unit of dust. Washed filter eMaze looks good. Tested system safety features. System doesnâ€™t have surge protector. With new wave of power outages recommend adding surge protection. Blower capacitor firstname.lastname@example.org ok for now. Hot surface ignitor ok 35ohms. System cycling on and off as requested.
Found this recirculating pump located in the garage was burnt out due to the main water to the home being shut off and the pump continuously running. We are going to be returning to install a three-quarter check valve on the cold feed coming into the water heater, a new recirculation pump, two half-inch ball valves and a hose bib.
Performed furnace and ac tune up. Zoned system with 2 thermostats. Attic access in upstairs hallway. Filter disposable 20-24-1. Tested system zoning.system working in rough shape. Furnace is 90 percent and doesnâ€™t have drain pan under it. If the furnace drain backs up itâ€™s going to leak on the attic platform. Furnace inducer collection box had a cracked corner. Inducer barely hanging onto unit. Heat exchanger has thermal stress see pictures. Cleaned burners and flame sensors. Hot surface ignitor ok. Ac runs and is cooling. Condenser dirty, washed condenser coils for better efficiency. Just not that efficient of a system. With age of equipment canâ€™t guarantee it will last much longer at the end of its life. Upstairs unit out of balance rattling, outdoor unit out of balance rattling. System showing its age. Furnace and ac tune up Maintenance plan.
Performed annual heating maintenance on 7 yr split Lennox furnace attic ac backyard. System has upgraded 5â€ filter in attic. Just replaced, found filter backwards. Flipped filter correct direction for client. Tighter attic, working on your side. Cleaned burners and flame sensor, parts look ok for now. Tested system for proper operation. Opened up unit and found door safety switch has been disabled, removed loose wire. Blower ok. Inducer ok. Hot surface ignitor ok. Flue pipe looks good. Checked electrical connection and control board for loose wires or burnt connections, ok at this time. Duct work is a mix of black flex and silver flex. Sealed. Tested heater output temp ok. Turned system to off position before leaving.Things to think about for the future. Due to all of these power outages, we can install a surge protector for your unit. To prevent damage to unit. Also your Membership expires in 4/5 months this is your last visit would you like to renew now?
Run camera th kitchen sink drain line to determine condition of pipe. Ran camera through clean out under kitchen sink to locate issue with pipe. Ran camera to source of issue 17 feet away. Line is separated with lots of roots. Line needs to be repaired. Will need to saw cut, jackhammer, and dig to expose line for repair.
Performed ac, furnace tune up Folsom. on a 26 yr old trane gas package unit ground, at bottom of house. Cycled furnace then ac. Performed furnace tune up, went thru and cleaned burners and flame sensor. No good way to see heat exchanger due to style of system. Capacitors ok. wiring ok. New board and new gas valve, just replaced. Performed ac tune up cleaned unit, wiped off debris ontop of unit. Tested refrigerant system running ok at this time, see picture. Checked dual capacitor ok. Checked indoor evap coil, starting to get build up, keep an eye on it.System has had a new control board and gas valve, and new capacitors. It has been maintained, thatâ€™s why itâ€™s still running due to its age. System is running good for now.If new owners would like they can call in and we can set them up on a maintenance plan, 159$ for a year of maintenance.
Customer has had warranty company try to fix his hot water heater, the heater occasionally shuts itself off and the customer has to manually start the heater. When a water heater is having intermittent issues like this you change out the gas control valve, the warranty company has only messed with the pilot assembly and thermal door switch. Installation of water heater was performed by the same warranty company and is lacking a permit. The water heater is supposed to have a drip pan but does not, the expansion tank assembly should be brass or stainless steel pipe but they used galvanized pipe. The assembly pipe is rusting and showing signs of degradation to itself and the copper water line that they attached to it which is causing electrolysis. Provided the customer with multiple estimates and he will contact us when he decides what he wants to do.
I had (MLK) to close the ticket. Miguel fixed condensate line. primary and emergency lines. Gas lines fixed they were reversed. all good to go.
Performed furnace tune up 10 yr Goodman split system Folsom. Tested system, put system thru itâ€™s stages, furnace running good at this time. Per client request look at drain line and secondary in attic. Pan is supported with 2by4 only on edges not in center pan sags. Would recommend sliding some center supports under pan. Not sure why pan is raised, just be for better slope. Pan and unit have float switch to kill power to unit if the pan fills with water. Checked gas pressure ok, cleaned burners and flame sensor. Variable speed motor ok changed filter for client. Hot surface ignitor ok. Black flex ducts sealed.slightly lifted unit and slide 2by4s under center of pan to support pan more. Slide one in from each side.Also renewed the membership for another year.Also cleaned off dirty hand marks on attic hatch as best I could.
We will remove old equipment and dispose per EPA regulations and install Up to 17 SEER/13 EER/80% 5 Ton American Standard 2 Stage Heat/2Stage Cool with True Variable Speed Blower. New drain pan, isolation vibration pads, new stainless steel gas flex, New pigtail, new condenser pad with vibration pads, perform nitrogen flush of the Refrigerant lines and perform a leak search down to 500 microns. New electrical disconnect, replace breakers. We will need to add a return plenum to accommodate adding a additional return to allow proper CFMâ€™s to allow the system to operate at full potential and pass the Title 24 testing that will be performed once installation is completed. Reseal all ductwork to Title 24 requirements. 2 year Crystal Blue Maintenance program included. Lifetime Heat Exchanger Warranty, 10 year compressor, 10 year parts, 2 year labor.
Customer shut off his main line valve and the shaft snapped and he stated the hose Bibb above was leaking. Upon diagnosis noticed the irrigation valve was leaking as well, customer also wanted to add on two angle-stops in the hallway bathroom. Removed the old valves on the water main, installed two ball valves for main to house and the irrigation. Installed new hose Bibb with vacuum breaker and two angle-stops in the hall bathroom. Turned the water on and there were no leaks, insulated the water main. Customer is provided a one year parts and labor warranty on there water main at the house and two angle-stops on the lavatory faucet in the hall bathroom.
Remove tub strainer on upstairs master bathroom to replace seal for purpose of stopping water leak into downstairs kitchen Removed basket strainer and rubber seals and replaced tub to drain seal and added new plumbers putty to upper strainer and re-assembled. Had customer run water while I checked underneath for leaks. Had customer run a little water then full volume for a couple of minutes, no more leak.
Performed diagnostic today, found clogged drain lines, primary into drain under sink. And secondary over bathroom shower. left quote to clear drain lines. They are going to have their maintenance man clear the drain lines. Left unit open so they have easy access. At this time it doesnâ€™t appear to need a new drain pan.
Performed ac Diagnostic 19 yr system. Found system appearing to be low on r22 refrigerant. System is 61ozs. System will need close to 3 lbs of r22 refrigerant. Refrigerant went somewhere might be a good idea to inject system with if dye to find leak.Charged system today, will return Monday and dye system then. System charged, well went from 0/125 to 62/172.
Corrections need to be made. Create separate job in project for appt for corrections
Completed plumbing maintenance,#no water heater is 20 years old it is showing signs of failure with Rust between inner and exterior tank, also has a failed expansion tank, Recommend to replace with a new 50 gallon gas Bradford white water heater. Found 11 plastic angle stops that should be replaced.
Performed annual ac maintenance on 23 yr old split downflow Goodman garage backyard. Tested all wareable parts. All in range. Dual capacitor 35-5. Electrical connections good. Contactor looks good. Inside blower compartment dirty. Normal ware for the age of system. Outside gave condenser a bath. Refrigerant levels ok, will need to keep an eye on super heat high. But system is working and cooling. Client only really runs upstairs zone, downstairs coils itself. Zoning ok, working for now.Due to age of system, want to watch the amount of money we spend on repairs.