HVAC Contractors and Plumbers in Rocklin, CA
When you’re looking for a professional plumber or HVAC contractor to help your home or business in Rocklin, CA, make sure you call a licensed and insured company with experience: Crystal Blue Plumbing, Heating & Air. We have been in business since 1976 and make it our goal always to deliver “Customer Service the Way It Used to Be! Customer Service You Deserve!”
We’re proud to offer the best home services to Rocklin including:
- Award Winning Plumbing Services
- Same Day Water Heater Replacement & Repair
- Sewer & Drain Clearing
- AC Repair & Replacement in Rocklin
- Local Heating Repair & Replacement
Our many services include air conditioning and heating installations, drain cleaning, repairs for water heaters, gas piping, and more. We offer 24–hour emergency service, 100% satisfaction guarantees, free estimates, and a personal touch you won’t find at larger contractors.
We Serve The Following Zip Codes in Rocklin, CA:
95678, 95677, 95663, 95650
Skilled Plumbers and Superb Plumbing Service
You never want to attempt to solve a plumbing issue in your house either on your own or with the assistance of a handyman who lacks training, licensing, and insurance. You must depend on professional plumbers. Crystal Blue Plumbing, Heating & Air has the licensed plumbers who will see you have the services necessary for a great plumbing system: new piping, bathroom and kitchen fixture installation, leak detection, sewer line replacement, and more. Our #1 focus seeing you receive the customer service you deserve in Rocklin.
for Rocklin, CA
Larry - Rocklin, CA
Keaton was very clean and did a good job, very informative and was good about changing out my filter and cleaning the louvers at the filter..
Via - Rocklin, CA
installation good service price ok
Tony - Rocklin, CA
Good sevice 7
Carol - Rocklin, CA
Mike was friendly and patient while showing me how to use my new product.
Mike - Rocklin, CA
Tyler did a great job
Evaluation of water heater
Lisa - Rocklin, CA
Shirley - Rocklin, CA
Installation was very professional and the price was decent
CJ - Rocklin, CA
Besides being pushy about getting paid right after installation the same day was not sitting well with me. After installation it needed to be fine tuned. I left messages afterwards about the situation with Mike, he told me that he would get right on the issue on hand. Did not hear from anyone for at least a month or more and by this time I’m upset about the way they were taking care of me. So I called again, and this time they sent Scott over right away. Scott is the man, he took care of everything that needed to get done right away with no hesitation what so ever and was very upfront with me and one hell of a nice guy. I wasn’t too happy with the company and I would not recommend them until I met Scott. He made things right and put a smile back on my face. He knows what he needs to do and gets it done while answering any questions that I had for him, explains things very clearly to me. Scott is the one that made me change my mind about recommending this company to anyone. Thanks Scott for making me believe in you and the company you stand for, I couldn’t be any happier and Satisfied with the work now. Scott should be head of customer service at all times! He is the one that could bring the company above the rest! Anytime I need service I always ask too send Scott out now and no one else. Thank you! CJ 😎
Jeremy was great to work with. He did a great job.
Roger - Rocklin, CA
I would recommend Crystal Blue Plumbing .
RoyceAnn - Rocklin, CA
Jeremy is a very good worker, he is very knowledgeable and very through
technician Taylor arrived on scene to investigate reports of a dishwasher blockage. Technician met with client sister who also lives in the home. client reported when she ran the dishwasher it began to back up into the sink. technician believes the blockage is in the garbage disposal or P-trap and recommends a garbage disposal clearing. Client agreed technician disassembled garbage disposal and P-trap. Technician found an excessive amount of food putting garbage disposal at once was cause of blockage. technician cleared blockage and reassembled P-trap. Technician tested to ensure no leaks. Technician cleaned work area of all trash and debris. Technician collected signatures and payment.
Technician will snake mainline from clean out access in driveway. Technician removed all raw sewage from area. Technician used drain machine to clear blockage at pop-up relief. technician found that after the drain was cleared there was still some residual back up inside of the downstairs shower and toilet. Technician was able to free up that blockage and wash out the area. Technician cleaned work area of all trash and debris and collected final signatures with payment.
Job PO is 5245090. Returned to install new vanity to cover up the plumbing in the bathroom of the garage, walked through with the rental owner and he approved the work with the property owner. Removed the wall mounted sink, removed the mini heater. Cleaned the walls, connected new water flex lines. Installed the new faucet and installed the sink over the top of the vanity. Screwed the vanity into the wall, and silicone sealed the back and side of the sink. Mounted the mini heater in the vanity cabinet, turned the water on with no leaks. Job PO is 5245090
Technician Taylor arrived on scene to meet with client and provide proposals for some remodeling. Client just purchased property in Rocklin off of Pacific Street that also contains a rear alley house. lient will live in the main house and his daughter will live in the back house. Clients main concern is with the bathroom setup in the rear home. It currently has a clawfoot tub with a small toilet and vanity in a small narrow area. Technician recommends removal of old tub and installation of new corner fiberglass shower insert. technicians will relocate shower drains and install new shower valve with shower trim furniture. This proposal is to replace clients existing tub for a corner shower stall. Technicians will demo existing tub plumbing and disposive properly. Technicians will open wall to access. Technicians will install new shower trap and risers through wall. Technicians will install new single handle pressure balance shower valve. Technicians will install new shower stall. Techn
Performed annual ac maintenance, signed back up on the yearly maintenance plan. Filter 20-24-1 ok shape. Ran system, system operational at this time. Gave condenser a good bath. Checked system refrigerant charge ok at this time. Capacitor ok. Client said hey might have something in attic, little critter. System older but running good for now. Ducts older flex, some of the air flow is varies. Will need to keep an eye on it.Resigning for another year.
Performed ac diagnostic unit is low on refrigerant, per pressures. Opened up wall hydronics unit and found oil staining on side of evaporator coil. With everything off heard refrigerant leaking. See pictures. Need to replace coil. Emailed options to manager. Talked to maintenance man.
Coils are extremely full of debris and dirt. Cleaned with coil cleaner. Tested system before maintenance to ensure all is working. Checked all electrical connections and are okay. Checked capacitor and is in range 7.9uf (7.5uf capacitor). Tested refrigerant levels and are showing 58psi LS and 174psi HS. Changed filter inside for homeowner. Did not want to renew membership at this time.Clean coils with heavy duty cleaner safe for condenser. This will improve the efficiency of the unit greatly. Cleaning coils provides better airflow to Cooling coils to ensure that unit can release the heat itâ€™s pulling from house. Not cleaning coils regularly can cause unit to overheat by working too hard to cool down refrigerant.
Performed ac tuneup in Rocklin. Unit is a Rheem rooftop package unit. Plenum are sealed and not leaking air. Checked coils And are slightly dusty but nothing stuck inside of Finns. Checked all electrical connections and showing no signs of burnt wires or corroded terminals. Checked capacitor and is in range 47uf/10.1uf and is okay. Cleaned out electrical compartment and removed dust and spider webs. Condensate is draining properly with no clogs and is draining into gutter. Gas line is hooked up properly. Will clean return grill and remove dust then replace filter.
Reviewed various options for making repairs to toilet we did confirm there is a leak on the toilet and according to our air-conditioning technicians there is an additional leak at the kitchen sink gave options to repair both customer had Bonnie out here a while back they made the repairs to the toilet he would like to contact Bonnie and have them come out and warrantee their work however if they do not warrantee their work he will be contacting us to come out and make the repairs properly
Return to complete job.
Maintenance of 8 refrigeration units (4 undercounter units, 1 standup freezer, 1 walk-in refrigerator A/H, 1 walk-in refrigerator condenser, and 1 ice machine ) Perform coil cleanings on all units inspected for proper operation and temperatures. Cleaning included - Perform simple condenser coil cleaning wiping down unit fan blades and vacuum out condensing side of refrigeration unit. standup freezer amp draws good, temperatures good. cleaned unit. Found condensation drain pan and wrong location. will cause water condensation to leak under unit and possibly cause water slip hazard. Installed condensation drain pan and proper location underneath drain tube for defrost cycle. Wine refrigerator working no problems no recommendations. amp draws good, temperatures good. Cleaning included - Perform simple condenser coil cleaning wiping down unit fan blades and vacuum out condensing side of refrigeration unit. under counter bar refrigerators (white wine drink refrigerator) thermostat not op
Would need to install remove and disposal of old equipment. Permit and title 24 requirements. Would install new air conditioning condenser and evap coil. Run new lineset under home. Run new drain line under home. Ran new electrical high-voltage due to existing power wire not big enough remove and disconnect existing ductwork for ammonia chiller AC system reconnected ductwork to Plenum as mobile home system was designed removing the excess ducts creating a high static pressure on system. To install evap coil had to modify front access door, modified drain port taped and sealed coil door sealed existing wall penetrations.
Out for estimate, 14 yr old carrier split system, r410a refrigerant. System operational at this time. Sticker starting to fall off. In attic 80 percent furnace. Zoned system with 2 returns, and black flex ducts ok shape.
- Shut water off to complex to and drain water heater - Remove existing water heater and dispose of unit - Modify existing water supply to accommodate new heater dimensions - Water heater installed at same location of existing tank type water heater - New water heater tested for leaks using building pressure - Gas supply piping modified to meet minimum safety standard - Water heater thermal expansion tank installed to replace existing leaking unit - Start up sequence and fine tuning adjustments included 3 YEAR WARRANTY
Have prepared multiple pricing estimates to include a tankless heater dual standard water heaters and 75 gallon pricing options will be emailed to Frank and he will discuss these options with corporate office Frank mentioned he can get back in touch with us within the hour after receiving emails contact later this afternoon will be made to get status of
Informed / showed customer how to use thermostat appropriately. turned off smart features adaptive learning so forth to allow customer to change thermostat as wanting to and not allowing thermostat to make changes
Customer noticed a water spout on the ceiling of her master bedroom closet, she had an hvac company out since they just had the unit installed but they told her it was a water line. Presented two options to the customer, repair in copper or in pex. Turned the water off to the entire home and drain the water out of the lines, cut the leaking pipe out. Installed two swing joints and a piece of copper pipe to make the repair, turned the water back on and bled the air out of the system. Checked on the soldered joints by tapping my channel locks on each joint to insure their strength, there were no leaks. Covered the copper lines back up with insulation and cleaned the insulation that got onto the floor of the home.
â€” DOUBLE BATHROOM FAUCET INSTALLATION â€”- Shut water off to existing two faucet - Remove four emergency water shut offs and dispose of - Provide and install four new â€œEZ Closeâ€ emergency under-sink water shut offs - Disconnect and water supply piping going up to faucet for removal - Remove and dispose of two currently installed faucet - Install two new STANDARD bathroom gooseneck faucet - Bathroom faucets include four new stainless steel braided water supply lines for long life - Test new unit with building pressure and by operating 1 YEAR WARRANTY
Customer had a water heater go out, upon diagnosis the glass on the chamber was broke and a thermacoupling was it through the seal on the burner assembly. Recommended a ew water heater and the customer agreed with the work, removed the old water heater. Installed the new 40 gallon Bradford White water heater, new gas valve and flex line, new water flex lines, new expansion tank, and strapped the tank to the wall. Connected the venting and the t&p, turned the water on with no leaks. Turned the gas on and the water heater lit perfectly.
Performed AC maintenance Checked capacitors 45/5 reads 43.6/4.9 Good within manufacture specs that +/-6%, amp draws good, refrigerant pressure good, perform simple water wash on condenser coil. operation system working perfectly. could not check drain line at this time due to COVID-19
Adjusted damper for bedroom to let more air in, also flipped one of the registers in the living room
I discussed various installation options with our premium passive standard faucets and budget faucets at customer incline to install two standard faucet without pop-ups
Out for ac inspections found 2 York air conditioning condensers form 1995. Upstairs and downstairs thermostats, upstairs unit has 2 20-20-1 filters. Downstairs unit has 2 20-20-1 filters. Upstairs unit is the left ac on the pad. Downstairs is the right ac on pad. Tested systems upstairs first, itâ€™s working fine then downstairs working as well.Upstairs. Unit visual inspection noticed loose wires from changed fan motor. The wires where making contact with the fan blade when the unit slowed down. Checked refrigerant slightly low. Could be low on r22 or could have a bad metering device. If cooling is effected need to add refrigerant to see if it helps. Dual capacitor 40 and 7.5, 7.5 low at 4.8. Gave unit a bath.Downstairs unit visual inspection ok. Checked refrigerant charge ok. Tested dual capacitor ok. gave unit a bath. Wires all tight and ok at this time. System running ok at this timeRecommend regular maintenance, see attached quotes for regular maintenance, comes with free
Customer wants the back bathroom to get a partial remodel, new insta-heater and putting the water lines back into the wall. Provided two options with either repipe great the plumbing into the wall or installing a new vanity with sink and faucet covering the plumbing that sticks out of the wall. Emailed the estimates and they will call us when they get approval to start the work, this is a two man job and can take all day.
Customer has a 7+ year old garbage disposal that stopped working, provided options for the customer and she called her son and they both agreed on a new garbage disposal install. Removed and disposed of the old garbage disposal and sink collar, installed the new garbage disposal and sink collar. Turned the water on with no leaks, turned the garbage disposal on and it works perfectly.