HVAC Contractors and Plumbers in Auburn, CA
You deserve to have the best heating, air conditioning, and plumbing for your home or business in Auburn, CA. And you’ve found the company to do it! In fact, the owner and his family are proud Auburn, CA residents! Crystal Blue Plumbing, Heating & Air is a full–service plumber and HVAC contractor in business since 1976. We provide all the air conditioning and heating services your home or business may need, as well as superior work for water heaters, drain cleaning, and more.
We are the go-to company for all home services in Auburn including:
- Drain and Sewer Cleaning Services
- Water Heater Repairs & Replacements
- Air Conditioning Repair, Replacement & Maintenance
- Heating Services
- Quality Plumbing Services
We’re fully licensed and insured, offer 24–hour emergency service and free estimates, and are committed to the highest quality customer service–”Customer Service the Way it Used to Be, Customer Service You Deserve!”
Call Us for Plumbing Service from Great Plumbers
Home plumbing is often more complex than most homeowners realize, which is why people often make the mistake of trying to fix broken pipes or other plumbing troubles on their own. We don’t want you to make this mistake, and you only have to reach out to the plumbers at Crystal Blue Plumbing, Heating & Air to have the quality service you deserve. We offer a full range of different plumbing jobs in Auburn, CA, from sump pump installation to slab leak detection and repair.
for Auburn, CA
Roger - Auburn, CA
Sean is a very knowledgeable & helpful service person.
Good Job! Thanks
Patty - Auburn, CA
The thoroughness is appreciated. Very knowledgeable and considerate.
Plumbing rough in with sean
Joel - Auburn, CA
Awesome!!! 5 stars Couldn’t be happier with my experience.
Diana - Auburn, CA
Great Service and certification completed!
Wayne - Auburn, CA
We were very pleased with Ken and Michael who is the company's Lead Tech coming out this morning to complete our work and insure that the Ducting Cert was completed satisfactorily. Once again it was done perfectly and of top notch quality! Thx very much Ken and Michael! Awesome job!
Great Company! Awesome Service! Best Price!
Wayne - Auburn, CA
We are very pleased with the overal experience we have had with this company! Ken was very fair and beat all other estimates by at $4000. The big box stores who came out to give estimates were quite a bit more. We just had the HVAC system installed and the work crew was amazing! Very professional and were prompt and installed without any issues. We couldn't be happier! Plus Ken had us preappoved for the loan in about three minutes. Beautiful! Finally our unit is working great in this 100 degree weather! Thank you Ken And to all the team who have treated us like royalty! We appreciate it!
Jennifer - Auburn, CA
Thorough and professional installation
Very knowledgeable and personable service and presentation. No 'hard sale' gimmicks!
Jennifer - Auburn, CA
Ken is an authentic representative and excellent source of information.
Professional, respectful, kind and efficient!
Ivy - Auburn, CA
Staci - Auburn, CA
This is my second experience with Crystal Blue, and both times they have done an excellent job. Their technicians are skilled, friendly, and clean. I’m not sure if they are the cheapest, but so far they have been the best. I will call them again.
Upstairs furnace. Tested system nest thermostat. System vibrates as well. Noticed inducer is loose from the shaft, bearing are most likely goin bad. Inducer has a lot to do with noise from system. Hot surface ignitor ok. Gas pressure ok. Checked electrical connections ok. Blower capacitor firstname.lastname@example.org. Blower compartment dirty/dusty fine dust starting to build up in system. Silver flex ducts sealed. High efficiency furnace draining ok. Ran system for complete cycle system ok. System back in the off position.
Living room furnace. Tested system, nest thermostat. System vibrates as well. Noticed inducer is loose from the shaft, bearing are most likely goin bad. Inducer has a lot to do with noise from system. Hot surface ignitor ok. Gas pressure ok. Checked electrical connections ok. Blower capacitor 10@10. Blower compartment dirty/dusty fine dust starting to build up in system. Silver flex ducts sealed. High efficiency furnace draining ok. Ran system for complete cycle system ok.
Performed annual heating maintenance on 3 split systems attic. Changed 3 filters, 20-20-1, 20-25-1, and 20-30-1.Master bedroom furnace, tested system. Nest thermostat. Once in attic, noticed system has a vibration noise, which can be heard in bedroom. Tested motor inducer motor assembly has vibration. Tested blower capacitor, email@example.com outside of manufacture recommend range. Recommend replacement. Checked electrical ok, board ok. Hot surface ignitor ok. High efficiency furnace draining ok. Silver flex ducts sealed. Gas pressure ok. Cleaned burners and flame sensor.Living room furnace. Tested system, nest thermostat. System vibrates as well. Noticed inducer is loose from the shaft, bearing are most likely goin bad. Inducer has a lot to do with noise from system. Hot surface ignitor ok. Gas pressure ok. Checked electrical connections ok. Blower capacitor 10@10. Blower compartment dirty/dusty fine dust starting to build up in system. Silver flex ducts sealed. High efficiency furnace d
Quote to install customer supplied faucet in break room. Customer also had concerns with dishwasher leaking, no issues with dishwasher at this time. Quote is flat rate parts and labor.
Customer stated that dishwasher drain line was leaking. Upon arrival found that disposal was full of food and air gap not installed right. Rubber seal was on wrong side of air gap allowing water to flow into cabinet space. Turned on disposal. To remove food waste and put rubber seal on proper side of air gap. Ran dishwasher to test for leaks. No more leak at this time. No charge to customer for service today.
Install three head ductless mini split 3 ton unit (1)18K head for living room, (2) 9k had one for each bedroom, all new electrical, one main multi zone condenser, with condenser pad. Iâ€™ll work done to manufacture standards and recommendations include three line set covers. This will provide true zoning and will heat or Cool each room individually or have the capability to all run at the same time. Up to 21 SEER for energy efficiency. Removal and sealing of old unit.
2 inch line is broken under the driveway will have to excavate up to 4 feet by 2 feet to make repair can not see break in line must be a fitting that has blown apart.additional work may be needed to locate bad section. No concrete replacment. Got down to the 2 inch abs pipe found cracked replaced section with abs and to no hub bands and backfilled area we exposed. We also ran camera from property line clean out 80 feet saw no issues but I was unable to see where it tie in to the cityâ€™s line it goes up hill from the city clean out so line is always under pressure. At this time tank is pumping and seems to be at normal function
Performed annual heating maintenance auburn. on newly installed gas package unit on the ground. Turned system on inside at ecobee tstat. System turned on, went outside to test system. Tested system safety features. All working at this time looked to see about noise clients hearing. We moved the transformer on a previous visit. Sounds ok to me at this time. Checked gas for leaks, none present, checked gas pressure, ok. Burners clean, flame sensor clean. Gave unit a quick bath. Checked sealed duct work under house, looks ok. System is running good at this time. System reached desired temp inside and cycled off, temp split of 37 degrees at registers. Installing a dedicated surge protector for the heating and air conditioning unit. This will protect your unit from the damage a surge can cause. It takes the hit so your equipment doesnâ€™t have to.
Roger is going to excavate drainage pipe and call us back.
Performed annual heating maintenance left side unit. Tested both system separately. First system took a long time to turn on.14-25-1 x 2 filters in hallway. But then system has filters next to unit. So system is double filtered. Only need 1 filter at unit 16-25-1 x2. So as to not effect air flow to system. Tested units safety features, lose of flame, ok. Lose of fuel, gas valves turned off correctly. Door switch taped closed on left unit Hot surface ignitor ok 55ohms and 57ohms. Left unit has a universal pressure switch. Right unit has factory pressure switch, both unit blowers ok. Checked electrical. All wires tight and ok. System running ok at this time. Inlet air temp at unit left 71, right 72. Output at furnaces 110. Temp rise ok. Cycled both units on and off, on there own. Tested air temp at registers. Some registers not in floor due to construction. This could effect airflow and temp.Recommend looking at surge protection for units.We now do back up generators
Performed maintenance on enviro propane stove. Light pilot, checked gas valve, checked adjustable gas valve working. Logs in back where there suppose to be. Some small amounts of dust burning off. Unit working at this time. Tested system multiple time, thru the controller. Controller is designed to work with tstat, client doesnâ€™t use tstat just the controller on and off. System working at this time.
â€”Basic Diagnosticsâ€” Examined install location and took photos for review Confirmed â€œgas smellâ€ by operating heater Customer â€œ the unit started smelling like shortly after install but not to this degree, it is perhaps associated with the cooler weatherâ€ Use gathered information to review with plumbing manager
Install with concrete pad and battery included, running of propane line and electrical to generator. Install automatic transfer switch and install full load to Generac panel. Run test and first year of service included.
50 gallon water heater is leaking itâ€™s electric dated 2005 will replace with a Bradford white water heater. Sub panel is within distance of unit. Installed new unit no leaks wrapped hot line installed new shut off valve
Performed annual heating maintenance auburn. Ran system got into attic, unit making clunking sound during operation flame looks good. Tested hot surface ignitor, 113ohms high keep an eye on it. Tested blower capacitor 7.5 ok. Blower buried behind flue pipe. Opened up coil door, to look at heat exchanger. Found big thermal stress marks on the heat exchanger. See pictures. Visual heat exchanger inspection ok. Changed filter.
Performed furnace tune up 17 yr Bryant gas package unit roof auburn. Went thru system today. System working in need of annual maintenance. Burner compartment full of bees and debris. Electrical compartment control board starting to show burn marks. Showed client pictures. Cleaned burners and flame sensor. Tested capacitors all ok at this time. Client informed us that bedroom colder than living area went in attic and found leaks in ducts see pictures.Recommend maintenance plan, if client want to keep u it running for longer.
Customer has 30+ year old water heater leaking from the bottom, presented multiple estimates. Customer refused to give email so no invoice was received. #no Customer was nervous about having a permit pulled.
Remove a few links out of the flapper chain and install a new kohler flapper. Tested and everything seems to be working, if the unit continues to run we will need to move forward with the secondary option of replacing the flush valve
Removal of old inducer, and replacement of the motor assembly. Removed old fiberglass gasket, and installation of a new one. Re wired in the new inducer, and tested system. System running much quieter. Client happy at this time.
Performed annual maintenance 22 yr trane gas package unit ground. Variable speed blower. Inducer making noise. Found out inducer is over amping and out of balance. Part is available in stock. Cleaned burners and flame sensors. System looks good clean for age. System running well at this time. Due to age of system recommend going over replacement options. Tried adjusting inducer to make it sound better. Changed filter for client. System intake air temp 80 supply air temp 125 at registers.Order part returning tomorrow 10-2 arrival to install inducer.
Will go over with wife sent estimate
Customer has a full sewage tank and the ejection pump is not working since the power got shut off. The tank is full of shit and canâ€™t get to the pump, let Customer he has to get the tank pumped and then have us out.
Duct test pasted, city inspection passed, job completed
Customer has a toilet she wants replaced in the hall bathroom, and a toilet in the master bathroom she wants rebuilt. Recommend the Kholer Cimmaron in the hall Bathroom, and a standard tank rebuild in the master bathroom. Left estimate with customer and her daughter and they will contact us when they decide what they want to do.