HVAC Contractors and Plumbers in Auburn, CA
You deserve to have the best heating, air conditioning, and plumbing for your home or business in Auburn, CA. And you’ve found the company to do it! In fact, the owner and his family are proud Auburn, CA residents! Crystal Blue Plumbing, Heating & Air is a full–service plumber and HVAC contractor in business since 1976. We provide all the air conditioning and heating services your home or business may need, as well as superior work for water heaters, drain cleaning, and more.
We are the go-to company for all home services in Auburn including:
- Drain and Sewer Cleaning Services
- Water Heater Repairs & Replacements
- Air Conditioning Repair, Replacement & Maintenance
- Heating Services
- Quality Plumbing Services
We’re fully licensed and insured, offer 24–hour emergency service and free estimates, and are committed to the highest quality customer service–”Customer Service the Way it Used to Be, Customer Service You Deserve!”
Call Us for Plumbing Service from Great Plumbers
Home plumbing is often more complex than most homeowners realize, which is why people often make the mistake of trying to fix broken pipes or other plumbing troubles on their own. We don’t want you to make this mistake, and you only have to reach out to the plumbers at Crystal Blue Plumbing, Heating & Air to have the quality service you deserve. We offer a full range of different plumbing jobs in Auburn, CA, from sump pump installation to slab leak detection and repair.
for Auburn, CA
Becky - Auburn, CA
Rachel - Auburn, CA
It was more than just a regular maintenance. I had many questions about my roof AND the unit and Scott answered everyone professionally.
Susan - Auburn, CA
Just wanted to say thank you to Scott Petty with Crystal Blue for his professionalism on the job. Knowledgeably answered all the questions we had, explained the process as he went through it, and left with us feeling confident about our system. Even though we only needed a maintenance service it is still nice knowing you have someone that is knowledgeable and can handle the problem if it were to arise. Easy to schedule an appointment, friendly staff and fabulous communication. If I were to need someone to help with our home heating/air. I would definitely call Crystal Blue again. Thanks for the solid work!
Wendy - Auburn, CA
Awesome experience! Helpful, professional - Samuel provided great communication and options for us. Thank you!
Ted - Auburn, CA
H2O estimate and service
Karen - Auburn, CA
Taylor Irik was personable and thorough. He covered the annual maintenance plan, which I intend to use.
Great service, awesome price
Jason - Auburn, CA
Our technician Jeremy very polite, explained everything clearly before the necessary work for the plumbing issue and the pricing without pressure. Highly recommended. End up getting the yearly service club.
Very good! 👍
Lisa - Auburn, CA
Very Thorough And Professional Service
Steven - Auburn, CA
This was our first plumbing service and we are impressed by how thoroughly they inspected all our plumbing. Great explanations, too
Staci - Auburn, CA
Scott was very nice knowledgeable. He explained why I was having issues with my heater, and showed me how to fix it, so that it doesn’t happen again in the future.
Returned to install new Kholer Highline toilet, removed the old toilet and disposed of. Installed the new Kholer Highline elongated ADA standard toilet, put a bead of silicone around the bottom of the toilet. Turned the water on with no leaks, flushed the toilet multiple times and its working perfectly.
Moving unit cutting in new shingles, removing patch, then resealing and sliding back together.
Technician Taylor arrived on scene to investigate reports the clients water pressure being low. Technician inspected pressure at husband and found it to be reading at 75 PSI. Upon further inspection technician found clients kitchen faucet to have a low amount of water volume. Client just had Crystal blue plumbing inspection performed day prior and everything was working fine. Technician believes that when the previous tech was out here exercising the angle stops debris from the rubber washer inside broke off into water system. Technician found rubber inside of kitchen faucet head slowing down the water volume and blocking up the jets. Technician recommends replacement of failed angle stops and flush of existing water lines. This proposal is to replace failed angle stops underneath kitchen sink as well as flushing all angle stops in home. Technician will supply and install new pull-down faucet. Technician Taylor departed to go acquire new faucet. Technician returned from supply house
Customer has a faucet that needs to be tightened down In the hallway bathroom, that is connected to a pop up Assembly that no longer works. Also there are two sinks in the home that have never been silicone. So we will silicone two sinks and replace the pop up assembly with brand new brush nickel pop up assembly to match fixtures finish. After that we will test for leaks in ensure that everything is working properly
Customer would like to check with her husband on various solutions for high water pressure water pressure approximately 80 psi (too high) threshold for unsafe water pressure 85 psi
Customer has a clog in his main sewer line, provided multiple estimates to the customer and he chose the standard snake job. Ran the snake about 40 to 50 feet and cleared the clog, ran a water hose at full pressure down the line for over ten minutes with no issues.
Customer has a toilet in the hallway bathroom that occasionally has a strong sewer smell coming from it. After checking the toilet I determined that the wax seal might be deteriorated, I also noticed the toilet is your bottom barrel Glacier Bay toilet. Presented multiple options to the customer considering that he told me this toilet gets the most traction in the home and they might want to update the quality instead of wasting money on a low end toilet. Emailed the estimates to the customer and he will talk with his significant other and they will contact us when they decide which job they choose.
Technician arrived on call back stating the drain is still backing up. Technician inspected and found a section of drain that was not hydrogen still had debris in it. Technician was quickly able to access the clean out and flush out all the debris. Technician tested laundry sink and the flow was returned to normal. Technician clean work area and pulled off.
Discussed various installation options with customer she would like to start with a minimum and work our way up as needed collected a down payment and scheduled for repair on Wednesday coming
Customer has a tub shower combo that takes forever to drain, presented options to the customer and he informed me he is a tenant. The customer will get approval with the homeowner and contact us when they want the drain cleared.
Talked to customer customer wants to do pro plan quarterly maintenance on four units please email over a copy to customer with just pro plan in there
Replacing the primary control board. Replaced primary control board, found old one had burnt up. See pictures, Tested system in fan mode, heat mode and ac mode... system operational at this time
Technician will open wall underneath kitchen sink to expose pipe. Technician will cut existing section of pipe. Technician will drill hole through exterior wall. Technician will install new exterior cleanout. Technician will then use hydrojet to clear secondary line.Technician Taylor scheduled hydrogetting for the following Tuesday. In the meantime technician access clean out underneath kitchen sink to perform a drain snaking with video inspection. Technician found a large buildup of grease the second he opened the clean out. Technician also was able to find a lot of grease within the first 20 ft of secondary line. Technician was able to snake approximately 45 ft to help clear up some of the debris. Technician will return on Tuesday to perform the rest of the installation and repair.
Performed annual ac maintenance 4 yr old Lennox split down flow system, closet side yard. Xc21, outdoor unit. Under oak tree cleaned top of unit cleaned condenser coils, and then cleaned compressor compartment. As well as electrical compartment. Cooler rainy/misty day refrigerant pressures lower, but ok and cooling well. Variable speed outdoor fan. Start capacitor for compressor ok. All electrical wires tight no loose or burnt connections. Ran system system cooled down and turned off on its own. High efficiency furnace. Changed 2x20-25-1 filters. One down stairs, one upstairs. Lennox zoning system.
Technician Taylor arrived done scene to investigate reports of a toilet leaking. Technician found toilet to be a one-piece glacier Bay that clients dated was installed about three years ago. clan stated that it appears it's been leaking for about 6 months now from around the base. Technician will pull toilet and inspect flange. technician will ensure everything is in good condition and install new wax ring. Technician will reinstall toilet with new hardware if necessary. Technician will steal around base with dap sealant.When technician pulled toilet he discovered the bolts to be extremely loose. He believes over time the shifting of the toilet because of how loose it is diminished the wax ring where it can no longer keep a watertight seal. Technician used extra thick wax ring with new hardware. technician tested multiple times to ensure no leaks before sealing with clear DAP sealer.
Performed furnace diagnostic split system attic. Found unit not working. Inducer turns on, burners light and then nothing. Fan not turning on. Tried to then turn just the fan on by itself. Nothing. Went in attic to see whatâ€™s going on. Blower cap 5 at 4.7 ok. I think itâ€™s the primary control board thatâ€™s bad.741.68 remaining balance due on completion of work. Afternoons work best. Will call Monday once I find availability.
Performed ac tune up mini splits 2 systems, Goodman/daikin for master bedroom. Fujitsu ducted 3 zone for rest of house. All return filters have just been changed. Washed outside units. Wants more air in master bedroom, and in master closet. Need to take air from laundry room to get more air into bedroom closet and bath. Flipped register in master closet for more air towards room. Air flow seems better. Cleaned filters on mini split power head master bedroom. 20-30-1 air handler makes noise when system runs a long time. Need to catch unit making noise to see why and whatâ€™s causing it. Motor is not hot to the touch. Nor does it appear to be touching anywhere...aWhen we install their quite cool whole house fan, we should do the neighbors roof repair. Same time, also might be worth it to adjust air flow at that time... need to catch
Performed ac tune up 9 yr old Goodman gas package unit ground. Visual inspection unit in ok shape. Cleaned out inside of compressor compartment. Electrical wiring ok found 1 connection that had almost come off, see picture. Dual capacitor email@example.com +- 5%. System doesnâ€™t have a hard start kit yet. System doesnâ€™t have a washable filter.Also went thru ac today, noticed furnace side of system burners pretty
Performed ac tune up 3 yr old split carrier package unit roof system tested parts all ok at this time. Unit leaking per client. Found that they kept the old stand and elbows, recommended removing unit and re roofing in new adjustable stand. All parts in range, and washed coils.This is an annual service plan, ac tune up, furnace tune up, plumbing inspection. Plus priority service and a 10% discount
Performed annual ac maintenance York split system. Washed filter 20-30-1. Tested system, system operational at this time. Tested system refrigerant ok r407c... r22 replacement, was changed when compressor was changed. System runs a piston. Visual inspection of unit finding condenser coils starting to show age keep an eye on them. Checked electrical connections all tight at this time no burnt wires or loose wires. Dual capacitor ok 80-5. Contactor ok. System has hard start kit. Gave unit a good bath. Put filter back in and cleaned anything I touched.
Gave options for removal and install of equipment. Emailed options for 5 ton split systems, 16 seer outside 80% vs furnace 2 stage, and 18 seer variable speed outside with 96% vs furnace 2 stage. Both units require zoning.
Out to install Trane xl19i variable speed outdoor fan motor. Removed cover, removed old bad motor, replaced motor. Put everything back together and tested system. System operational at this time. Ran system 15 min no problems.
turned on unit from thermostat variable speed motor for blower came on went upstairs to check operation of the unit found unit operating with no problems. checked outdoor unit found condenser fan motor not operating rocking back-and-forth internal control went bad needs new condenser fan motor
Customer has a kitchen sink that clogged last night and they did not put anything substantial down it. Ran the kitchen snake down the cleanout located underneath the sink, got about 40 to 50 feet before the line stopped filling up. Ran the water down the line for 10 to 20 minutes with no issues, customer would like to schedule his AC and plumbing preventative inspections.
Performed annual ac maintenance 3 split systems 2 in master bedroom access one in upstairs closet access. Watch tree growth next to unit.Unit 1 cleaned outside of unit, washed condensers, visual inspection of parts. Tested parts, Contactor ok, dual capacitor ok. All wires tight and ok refrigerant pressures ok.Unit 2 cleaned outside of unit, washed condensers, visual inspection of parts. Tested parts, Contactor ok, dual capacitor ok. All wires tight and ok refrigerant pressures slightly low keep an eye on it this summer if it struggles to keep up call us out.Unit 3 cleaned outside of unit, washed condensers, visual inspection of parts. Tested parts, Contactor ok, dual capacitor ok. All wires tight and ok refrigerant pressures ok.Changed filters for all 3 units.This is for all 3 heating and air systems and the tankless water heater