Citrus Heights CA
HVAC Contractors and Plumbers in Citrus Heights, CA
When you work with a plumber or HVAC contractor, do you feel you don’t get the customer service you deserve? We understand your frustration! That’s why our motto at Crystal Blue Plumbing, Heating & Air is “Customer Service the Way It Used to Be, Customer Service You Deserve.”
We’re proud to provide Citrus Heights with exceptional home services including:
- Plumbing Services
- Water Heater Services
- Drain Cleaning Services
- Air Conditioning Services
- Heating Services
We’ve been in business since 1976, but that’s not the only reason to trust us with your air conditioning, heating, and plumbing needs. We offer free estimates and 24–hour emergency service. So whether you need drain cleaning, options for water heaters, or maintenance for an AC, you can look to us. We’re fully licensed and insured.
We Serve The Following Zip Codes in Citrus Heights, CA:
95610, 95611, 95621
Plumbers Ready to Help with Your Household Plumbing System
No matter what assistance you need with your plumbing in Citrus Heights, CA, you can rely on our licensed plumbers to take care of you. Don’t attempt to make plumbing repairs yourself, and don’t trust to a “handyman” who lacks proper licensing. You must have professionals to ensure any job–from fixing a leaky faucet to installing new bathroom appliances–is done correctly. We’re focused on seeing you receive complete satisfaction with the work we do and enjoy peace of mind.
for Citrus Heights, CA
Excellent service, expertly done.
Mario - Citrus Heights, CA
This is the source for tankless water heater service. The technician knows the product inside out and will tell you what he's doing every step of the way.
I had a phone conversation with Sean. Is this a fitting setting for a review?
Don - Citrus Heights, CA
Knowledgeable and extremely competent service. Thank-you, Scott.
Don - Citrus Heights, CA
Knowledgable and helpful.
Andrew - Citrus Heights, CA
Finally knowledgable and professional service.
very good and at a very good price.
Robin - Citrus Heights, CA
Great Service! worth every penny
lee - Citrus Heights, CA
Good Service and Good Work
Brenda - Citrus Heights, CA
Excellent Service, Knowledgeable Technician
brenda - Citrus Heights, CA
Sean did a nice job replacing my garbage disposal and re-working the faulty plumbing. He took time to show me what he was doing and how he was making the repairs. He was very efficient, polite, and completed the installation without having to go back to the shop for parts. Overall, a good experience and I would use them again.
Service in less than 20 minutes
Sue - Citrus Heights, CA
Great service and had my water back in the same day.
Awesome service !
ho - Citrus Heights, CA
Performed ac diagnostic, unit is original. Found unit leaking water and water was coming out of the left side... drain on the right side. Resloped unit, for better drainage and system appears to be better. Maintenance to go back out and reseal the unit tomorrow. Now that the unit isnâ€™t leaking as bad. Canâ€™t guarantee fixed. But better. If problem consists will need to retrofit unit. po50-307
Installed new 1 inch pressure regulator valve on main water line, rebuild main riser with new tea, hose bib, Ball valve with secondary ball valve for irrigation line insulated pipe,checked pressure and set for 60 PSI.
Performed ac diagnostic on unit found system low on refrigerant. Inspected system for refrigerant leaks, no oil stains or residue. Charged system with client supplied refrigerant.If problem consists will need to dye system with uv dye to try and find leakPo 50-307 Need to properly charge system. Checked system for big leaks everything looks ok. No oil stains or residue. Properly charged system see before and after photos.
Would remove old equipment and replace with customer supplied equipment.
Performed quality check and installed 1 20-25-1 filter inside unit. Sealed up insulation around coil unit. Unit making slight noise at high speed air conditioning. Noise got better with filter inside unit.
Found unit not working breakers off, turned on breakers and turned on dissconnects, tested for power had air handler turning on, on its own. And had heat pump outside not getting low voltage. Fixed outside units low voltage. Re wired unit and system came on when it was suppose to. Cleaned up around heat pump. Put everything back together. And tested refrigerant. Apt was at 75 cooled unit down to 71. Turned off portable unit. And shit sliding door.
Replace 1.5 ton heat pump with customer supplied equipment
Made install corrections, adjusted unit positioning. Fixed refrigerant leak, Added new filter dryer. pressure tested system. Vacuumed system, than factory charged system. Balanced refrigerant. Uv taped lineset. Labeled disconnect for max fuse size. Fixed flue.Need to wait till adt alarm text comes out to see whatâ€™s wrong. We cut alarm power. Not sure what needs to be done to fix it. Alarm tech to come out 12-4 today.Stayed to make sure system was up and running, and cooling before I left.
Flush tankless water heater per manufacturer recommendation. Unit is located in garage next to HVAC unit. Unit is equipped with bypass flush valve kit, hooked up flush kit an approved descaler to remove debris from heat exchanger. Ran product through unit for 45 minutes. Also removed and cleaned filter and flowrator. Tankless water heater is not showing any error codes and does not have any prior codes in memory. Unit is in good working order.
Performed ac diagnostic found system struggling to start on cool morning, hooked up refrigerant gauges and found system appears to be over charged. Added start kit supplied by customer to get system started and 111/300 for r22 system at 75 degrees, removed refrigerant got numbers to 80/199. Unit cooling 58 degree air coming out of vents. Refrigerant lines sweating. Po50-307
Performed Ac diagnostic found which system it was outside, then blown fuse, then low compressor capacitor. Then system changed part. Then added hard start kit to get system up and running. Then found system low on refrigerant. Added some refrigerant, and found leak in outside unit. Inside where a wire appears to have rubbed thru the copper.Recommend replacement of system. Due to age and cost of repairs.Po50-307 Perform ac diagnostic to see what it will take to get system running.
#nn Flue pipe broken do to forcing it in place, leak in suction line possibly one and discharge line, no glue on PVC, gas trap located in wrong spot, screen venting for air vent is not reinstalled in place, there was no need to cut and in large the whole backside of return box and side of furnace stand weakening stand airflow for return wouldâ€™ve been plenty big enough with the 10 x 24 sheet metal duct. needed more airflow through return grill itself and return filter grill was the wrong one that was installed shouldâ€™ve been standard stamp faced return grill. filter needs to be installed in furnace due to other return cut in the return box did not install filter rack clips that come with the furnace to install filter have no idea where clips are. Service disconnect does not have max fuse amp written on it. system is ordered and supplied with new condenser pad and was not installed New condenser is bigger than old condensing pad. condensing unit was installed too close to house ma
Performed ac diagnostic, heat pump original air handler, with r22 nordyne heat pump. Found inside running outside compressor not turning on. Compressors electrical test ok mechanically seized wonâ€™t turn over. Tried to start it with start assist.Need to replace whole unit due to age and shape. Po50-307
We will remove old equipment per EPA regulations and install a 4 Ton 16 SEER/13EER matched with a 80% Up flow furnace with a constant torque blower motor. Enlarge side wall return to 20 by 24 with stamp face Grill. Filter rack included. New gas flex, new electrical disconnect and whip, pigtail included. New thermostat included. Condenser pad will be included. New furnace stand with filter rack. Title 24 and permitted. 500.00 Smud rebate plus 50.00 rebate for Nest thermostat
Performed ac diagnostic Citrus Heights. Air handler 34 yrs old with newer heat pump. After getting permission to renter apt. Went in and found system in off position turned system on and system turned on right away. Ran system for over 15 min straight apt cooling well at this time. Refrigerant pressures ok. System looks good for now. Nothing wrong at this time. Apt cooled from 80 to 78. Cycled system off and then back on. System ok. Left system on and running at 78 degrees. Back lite on tstat stay on all the time. Po50-307
In Citrus Heights We will remove old equipment per EPA regulations and install a 4 Ton 16 SEER/13EER matched with a 80% Up flow furnace with a constant torque blower motor. Enlarge side wall return to 20 by 24 with stamp face Grill, new furnace stand with side wall plenum. Filter rack included. New gas flex, new electrical disconnect and whip, pigtail included. Nest thermostat included. Condenser pad will be included. New furnace stand with filter rack. Title 24 and permitted.
Performed ac diagnostic Citrus Heights. 26 yr split carrier closet backyard. Found system turns on and runs then doesnâ€™t work as well. Hooked up refrigerant gauges and found system low on refrigerant and as it ran the number got worse and worse. Which explain how the system looses air flow. So itâ€™s either just low on refrigerant or itâ€™s got a bad metering device. Would need to add refrigerant to see if itâ€™s low on r22 or a bad txv.Client wants to think about it, knows she needs a new unit but doesnâ€™t know what to do. Doesnâ€™t want to through money away. And no guarantee adding refrigerant will work.
Run cable through two way clean out towards home to unclog. Clean out is on left side of home, ran cable approximately 3 feet to blockage and stopped as guest hall bath is very close to clog. Line cleared easily with little visual waste. Ran lots of water through line to test that it is clear. Line is clear
When water heater was replaced, t and p drain line had 3/4â€ inch flexible cooper pipe in its length of tubing. Flex pipe is not code, removed flexible pipe and replaced with 3/4â€ rigid copper pipe per code. Technician sees no other issues with water heater install. Waiting on inspector for final inspection approval.
Remove old equipment per EPA regulations and install 2 Ton customer supplied split heat pump, closet and in front. Need filter drier. They have disconnect and whip. We will install the equipment, pressure test, vacuum system And then factory charge system with customer supplied refrigerant. Customer is responsible for all permits and inspections.Soonest available right now is Tuesday the 20th.
Sacramento ca AC service diagnostic AC not working Perform diagnostic on AC system found no low voltage power at outdoor unit determined it was caused by thermostat. replaced thermostat tested unit operation found no other problems at this time.
Called don will get on sch when material arrives
Performed diagnostic. Found system working inside not working outside, newer r22 system. Has leak. So we dyed system with uv dye to try and find leak. Charged system back up with customer supplied r22.Pressures NOT holding for now. Went thru system inspecting for dye at connection points/brazes. And at coils inside and outside. Found two leaks outside at the Schroeder core on the suction side. And inside the coil found leak at bottom right side.Po 33584Quoted for system replacement with customer supplied equipment, emailed quote over.
Performed ac diagnostic. System not operating at all. Tested system and found tstat not doing anything. Changed tstat with customer supplied one. And system turned on. Airflow appears weak, but system is on and cooling at this time. Tested ac system now that itâ€™s up and running, found unit low on charge.Po50-307