Citrus Heights CA
HVAC Contractors and Plumbers in Citrus Heights, CA
When you work with a plumber or HVAC contractor, do you feel you don’t get the customer service you deserve? We understand your frustration! That’s why our motto at Crystal Blue Plumbing, Heating & Air is “Customer Service the Way It Used to Be, Customer Service You Deserve.” If you live in Citrus Heights, call Crystal Blue today and see why our customers love us.
We’re proud to provide Citrus Heights with exceptional home services including:
- Plumbing Repair Services
- Water Heater Replacement & Repair
- Professional Drain Clearing & Rooter Service
- AC Installation, Repair & Maintenance
- Heating Repair & Replacement
We’ve been in business since 1976, but that’s not the only reason to trust us with your air conditioning, heating, and plumbing needs. We offer free estimates and 24–hour emergency service. So whether you need drain cleaning, options for water heaters, or maintenance for an AC, you can look to us. We’re fully licensed and insured.
We Serve The Following Zip Codes in Citrus Heights, CA:
95610, 95611, 95621
Plumbers Ready to Help with Your Household Plumbing System
No matter what assistance you need with your plumbing in Citrus Heights, CA, you can rely on our licensed plumbers to take care of you. Don’t attempt to make plumbing repairs yourself, and don’t trust to a “handyman” who lacks proper licensing. You must have professionals to ensure any job–from fixing a leaky faucet to installing new bathroom appliances–is done correctly. We’re focused on seeing you receive complete satisfaction with the work we do and enjoy peace of mind.
for Citrus Heights, CA
Showed up quickly & did a wonderful job!
Amber - Citrus Heights, CA
I called because I had a clogged toilet. The response time was super quick. Taylor was at my house in about an hour. He worked hard to clear the clog. It was my daughter’s wipes that clogged my plumbing. He pulled them out and fixed the problem. He was very nice and professional. I will definitely be saving this number to use in the future. Thanks a million. You saved the day.
Wayne - Citrus Heights, CA
Taylor was great professional and explained all the repairs and gave us options. Overall experience was excellent.
Great to work with!
Joe - Citrus Heights, CA
Customer service was excellent and they did a great job
So Accommodating and great service
Debra - Citrus Heights, CA
Fast and easy appointments and they were very accommodating by working with my schedule. Taylor, my technician, kept in contact with me via text while I was at work and payment was easily made via email.
Great service, great customer service
Jeff - Citrus Heights, CA
The service I received today from Crystal Blue Plumbing, Heating and Air was awesome. From making my phone call to them, to having the technicians arrive and take care of my issue, the experience was great. They handled our issue very professionally and were very polite and respectful. Should we have a need for help again they will be getting the call.
Nicole - Citrus Heights, CA
The initial call for service was fast and friendly. I was given a 4 hr window and Chris showed up 30 mins into the window which I was super pleased with. He came in and was friendly, knew what he was doing, took his time and explained everything to us. We will absolutely be using crystal blue for any future plumbing issues we hope won’t arise. 🙂
Deborah - Citrus Heights, CA
Plumbing review was positive.
Don - Citrus Heights, CA
No problems with the sevice
Juan - Citrus Heights, CA
Ken shows great customer service skills and easy to get his point accross
I am very satisfied regarding the degree of service rendered on kitchen drain.
Don - Citrus Heights, CA
Removal of existing non functioning heat pump, and replacement with customer supplied equipment. We will nitro braze and pressure test and factory braze unit. Also going to reconnect to existing duct work. Installing customer supplied disconnect and thermostat.That system was damaged, and we had to come back out and install another heat pump for that unit. Removed damaged unit to go back, installed new heat pump, pressure test, vacuum and charge system. Unit running on departure. Tenant happy. Showed maintenance system operational.
Goodman condenser on apt #7 came damaged and is leaking out refrigerant. The unit is new and should be replaced by manufacturer.I have model and serial numbers of unit for replacement for senior tech to communicate with office.
Everything working no problems found piston correct size
Performed diagnostic found bad compressor capacitor, gas package unit roof. 40 mfd cap at 1. Client to replace part. System is only a few years old and has had some work done to it. New condenser fan motor.
Customer has an electric cooktop stove that they want to convert to a gas cooktop, home has gas supplied to it and the meter is in the front middle of the home. Length of pipe would be 75 to 100 feet of piping underneath the home, run half the line in 3/4 and 1/2 inch on the other half. Permit will be up to the customer to obtain, they will contact us when they decide to get the work done.
Emailed estimate for equipment change out
technician Taylor arrived on scene to investigate reports of kitchen sink blockage. client stated this has happened once in the past. client lives in a single story home on slab from the 1980s with original cast iron sewer system. client does have exterior clean out behind kitchen sink. technician recommends snaking and hydro jetting as well. technician will access secondary line clean out behind kitchen sink and use small drain machine in order to attempt to clear blockages. technician use secondary drain machine through clean out to attempt to break up any blockages. technician was able to smoothly snake line without any major blockages present. technician believes problem is just grease buildup and highly recommends hydrojetting. technician tested drains to ensure flow was proper.
Out for ac diagnostic, found unit low charge. Tried to charge system found added 1/2 lb of r410a pressures skyrocketed. Need to replace metering device, need to figure out what size and get it. Also need to see if we installed it.Need to find august 20th instal
Performed commercial diagnostic, split heat pump outdoor unit not working. High voltage tripped breaker. No power outside on arrival. Condenser fan motor sounds horrible. Tested to see if compressor is trying to turn on. Pulling amps not starting. System has refrigerant. Holding 300+ psi. Going to see if compressor is over heating, or if a hard start kit will get it moving.Fired system up it ran for a few seconds and then stopped.Unit turns on and runs for a few seconds then as the high side pressure climbs it trips. Removed some refrigerant, system turns off before the high side climbs to high.Po 48990
Previous plumber was out working on the water main and now a fitting is leaking, upon diagnosis I noticed they threaded a metal fitting into a plastic fitting which cracked. Made repairs to plastic fitting and replaced with brass to ensure failure does not repeat
tech Taylor arrived onscene to investigate reports of drains backing up. tech found the best access to be the kitchen clean out and was able to snake from there. this proposal is to snake client secondary line through kitchen clean out. tech successfully cleared line and demonstrated to client. technician collected signatures and payment.
technician arrived and found that client had toilet back up immediately after technician augured a few days prior. technician stated we would start with augering again to attempt to clear anything otherwise we may be looking at additional charges to pull the toilet and attempt to clear blockage that way. technician was able to use auger through toilet three additional times until the flushing was smooth every time it was tested. Work was demonstrated to client who was very pleased with results. technician clean work area and pulled off.
Performed annual a.c maintenance in Citrus Heights. Unit is a Rheem rooftop package unit. Unit is 5 years old. Condensing coils are free of dirt and debris. Checked all electrical connections and are okay. No damaged or loose connections. Checked condition of contactor and is working properly. Checked capacitor and is in range showing 51/5.1uf and is rated for 50/5 +-6%. Checked blower motor and is okay no dirt buildup on fan blades. Checked refrigerant levels r410a and are showing 115psi Lowside and 239psi Highside. Refrigerant levels are okay.Tested unit after maintenance to ensure proper operation.
technician Taylor arrived on scene to perform annual maintenance inspection. technician began by flushing 50 gallon water heater located in the garage. technician then checked off the kitchen and laundry followed by both bathrooms and sharing all drains and sinks were offering properly. technician answered questions clients had about their old pipes. client said they might want us to come back out to do an inspection under the home and possibly support some loose pipes. technician will supply proposals for client to review.
Performed annual ac maintenance, 5 yr old split system closet back yard. Return under unit 12-24-1 small. System should have more air flow, only way to accomplish that would be adding a second return on the side of the unit. This might also make the unit quieter while running. Gave unit a bath with water to clean condenser coils. Washed unit top to get dirt off. Checked electrical connections all wiring tight and ok at this time. Checked refrigerant pressures ok, they are above freezing on a cooler morning temps in the 70â€™s. All parts within range at this time. Dual capacitor email@example.com... keep an eye on it. At 5 yrs could be dropping out of range soon. Resigning up for another year of maintenance
Out for estimate on gas package unit rooftop, quoting a 4 ton 14 seer single stage heat, single stage cool. Ducts original to home can not gaurentee it will pass title 24, if we donâ€™t replace ducts in attic. Hard pipe ducts in attic, see pictures. Rooftop package unit would need a crane, we would also need a new adjustable roof curb. Reflashing the new curb into exsisting roofing to seal unit. We would pull permits and title 24 testing for client, they would be responsible, if we donâ€™t do the duct replacement for any costs associated with passing the title 24 testing. We would replace the whip and disconnect on roof, run the gas line to code, and also rerun the condensate drain line as well. New digital programmable thermostat.
technician Taylor arrived on scene to investigate reports of fill val ve not working properly on toilet and another toilet that would not drain properly. technician was able to diagnose that the angle stop and supply line of the toilet were in proper condition and that the fill valve had been blocked up by something and no longer operable. technician recommends replacement of the fill valve and client accepted. client also stated since she moved in a toilet in the other bathroom has not flushed properly. technician inspected and recommend auger service to attempt to clear blockage. client agreed to proposal. technician performed all work per estimate and documented with photo and notes. technician clean work area of all trash and debris. technician demonstrated work performed to client. technician collected signatures and payment.technician will uninstall existing fill valve in master bathroom toilet. technician will install new fluid master fill valve. technician was supply a compli
Technician will procure parts and repair left vanity master bathroom sinktechnician Taylor arrived on scene supplying parts necessary to complete faucet repair. technician shut off water to faucet and master bathroom. technician disconnected supply lines and uninstalled original hardware. technician installed new hardware for the cold handle. technician connected existing supply lines and tested to ensure no drips. handle shuts off faucet 100% and was set to the proper depth. technician clean work area of a trash and debris. technician collected signatures and payment.
Found outside unit not turning on, compressor in the caution zone, keep an eye on it. Changed capacitor, 15@5. Tested system, Running. Let it run for a bit, running on departurePo 48204
Technician Taylor arrived on scene to investigate reports of a dripping faucet and two toilet malfunctions. Technician found both toilets to have fill valves that are failed or failing. Client also has the left sink of the master dual vanity dripping due to a failure in the cold handle. technician inspected to see if the cartridge could be replaced and found this faucet to not use a cartridge. Technician was able to locate replacement parts and will provide proposal for repair. Technician provided clients with the crystal blue advantage and scheduled work.
Out for partial duct replacement options, ducts werenâ€™t done correctly recommend replacing and or repairing all ducts in attic. Need to rework the hole set up.
Performed ac diagnostic found system not working, wet switched tripped again, secondary drain pan dry. Reset and system turned on. Senior technician advised me to elevate switch in pan, so trying that switch working at this time. Will want to keep an eye on system for awhile. Ran system for awhile nothing going on wondering if the primary drain backs up? Find problem and test system.
Technician Taylor arrives to provide proposals or sewer repair. Clients dated about 18 years ago he had a trenchless sewer replacement in his front yard. In recent years he has experienced multiple backups that have been discovered to be caused by an offset where the polyurethane pipe ties into the original cast iron. Technician will supply proposals for excavation and possible repair costs. Client requested proposals by email.
Replace old r22 converted equipment with the customer supplied r410a heat pump and air handler. Changed metering device to match. Pressure tested system, vacuumed system. Performed charge rite. Re hooked up condensate drain lines of new unit to exsisting lines. Re did transition to duct work to fit new unit. Tested system, system cooling.
Compressor replacement removal of old compressor, filter dryer and electrical plug harness for compressor. installation of new compressor new filter dryer relocated filter dryer to outside of condensing unit to allow for easier service. Installed new electrical compressor harness. inspected system for premature failure of existing compressor found possible cause piston never changed out when unit was installed. this could cause premature failure of new compressor if not corrected. warranty is void recommend correcting proper piston size to allow for compressor to operate at proper pressures and temperatures.