HVAC Contractors and Plumbers in Roseville, CA
When you call for a plumber or HVAC contractor, you want the most skilled people to show up at your home or business. If you live or work in Roseville, CA, calling Crystal Blue Plumbing, Heating & Air is the quickest way to ensure you get the best! We’re a licensed and insured plumbing, air conditioning, and heating contractor, and have been in business since 1976.
We’re proud to serve Roseville and provide the best in home services including:
- Local Plumbing Repair
- Same Day Water Heater Replacement
- Rooter and Drain Cleaning Services
- Central AC Repair & Replacement
- Professional Heating Repair & Replacement
Customer service is our #1 priority. It’s why we offer free estimates and 24–hour emergency service. From repairs for water heaters to drain cleaning, our employees are committed to meeting your needs with “Customer Service the Way It Used to Be! Customer Service You Deserve!”
Our Plumbers to the Rescue! We’re Your Roseville Plumbing Pros
Indoor plumbing is part of daily life, and it’s a part of our job to ensure you have a convenient daily life. You might need leaks found and fixed, a new kitchen sink installed, or routine plumbing system inspections. We can do all of this at Crystal Blue Plumbing, Heating & Air. Our plumbers are licensed, insured, and best of all they’re highly trained. As with our HVAC services, we want to go beyond simply fixing problems. We want to solve future problems for your household!
for Roseville, CA
Gerard - Roseville, CA
Air Duct Replacement
Cathy - Roseville, CA
Brian - Roseville, CA
Our technician, Brandon Bury, was the best.
Barry - Roseville, CA
Our technician, Brandon Bury, was the best. He was personable, he was efficient, he was considerate to cover his feet when he came in to the house, and he really knew what he was doing. I hope we don't have another plumbing issue but if we do I would sure hope Brandon would do the repair. I do think the pricing by Crystal Blue Plumbing is high. Otherwise, I would give five stars for overall experience.
Good price on a good system
Dennis - Roseville, CA
I was very happy with the price and installation of my new HVAC system. I would definitely recommend Crystal Blue to anyone looking for a quality install at a fair price.
Dorothy - Roseville, CA
Scott was very knowledgeable and explained everything in detail. Very professional and a really nice guy. Would definitely do business again with them.
David - Roseville, CA
Early and very easy to talk to. I would recommend them to everyone. Scott is great!
quick response, got everything fixed
Dennis - Roseville, CA
Outstanding, Friendly and Professional
Daniel - Roseville, CA
Chase was on time and, in a very friendly, professional manner, quickly fixed my plumbing issue. We are so grateful to have our shower working again.
Really nice people. Very professional.
Alethea - Roseville, CA
Had some work done and it was a very easy experience.
Stood inspection for duct testing. duct testing pasted, airflow pasted refrigerant charge pasted. Ready for city inspection once customer receives permit packet from Crystal blue which should be coming in the mail. once customer receives packet there is a phone number for customer to call for city inspection if customer would like us to Stand inspection that day we would ask to let us know what day it is couple days in advance. crystal blue does not need to stand inspection. If customer has any questions in regards to the process or how the system is operating please call.
Customer stated after last service rendered low water pressure at all fixtures throughout home. Upon arrival tested two different fixtures water volume pressure was good at first and then lowered. Technician forgot to turn the water supply to home back on at full volume making water pressure throughout home low. Turns gate valve for water supply to home back to fully open water pressure is now good. No charge to customer for service today.
Customer has a clogged kitchen sink and a slow draining lavatory faucet, snaked the kitchen line clearing the clog. Ran water down the line for over ten minutes with no issues. Pulled and cleared the pop up assembly at the master bathroom lavatory sink, tested and the drain keeps up with the faucet.
Customer is remodeling master bathroom and shower valve needs to be relocated to flush mount in wall. Returned on Friday, November 8 at 8 AM to relocate shower valve and shower head and wall per customer request. Shut water off to home and cut hot and cold water supply lines to shower valve to relocate. Also extended height of shower head to 7â€™6â€. Valve is now set for proper distance for tile to be set and has been tested for leaks. No leaks at this time.
Out to perform annual heating maintenance, split system. Changed filters for client. Inspected unit, tested system heater turns on. Older furnace, dedicated horizontal. Rheem. Went thru system removed blower so I could get a visual of the heat exchanger. Lots of thermal stress and rust, but holdinging for now. Grey flex ducts ok. System might have backed up and went out secondary again. Good for now. Check during next visit. Due to age of furnace want to watch out for repairs. No real return on investment working on equipment that old.Emailed pictures and videos of unit.
Customer has a tankless unit around 10 years old and it had a 13 error code, intake exhaust failure. Upon diagnosis the intake was an open pipe on the top of the unit and could get dust into the unit. Customer provided a can of air and I cleaned the exhaust fan from the dust. During the cleaning I tested the unit and ran it multiple times with no error code present, unit is working fine at this moment. If need be and the unit faults again we will come back out for a deeper diagnosis but the unit seems to be working fine at this time.
Customer wanted quote to have vent piping for existing water heater installed and to go out the roof instead of through the side wall of home. Unit is a jacuzzi brand and according to install Manuel can not be vertically vented. Gave customer quote to have new unit installed to accommodate customer needs. Quotes flat rate parts and labor. Quote is good for three months.
Repair leak in tub faucet with customer supplied part. Tub is a Roman type delta two handle valve. Customer had parts sent by delta and called to have us install. Had to shut water off to home to make repair. Installed new washers and springs for both hot and cold cartridges. Turned water back on to home to check for leaks. Faucet does not leak anymore.
Customer stated that water heater was not working, upon arrival found pilot lite to be out. Customer stated that water heater has been off since new HVAC system was installed. Went through start up process and water heater is working fine. No charge to customer for service today.
This would include removal and disposal of 1 return and 12supplies. Plus adding a new return duct to give system proper airflow. Add new return plenum. We would also replace return air filter grills so the match. We would run new flex r8 ductwork. We would also keep existing registers because some of them are painted to match. plus re seal plenums and collars. And permits and title 24 testing.And repair condensate drain lines. At same time, by cutting whole in platform for the ptrap to sit in.Also needs us to remove holiday items form attic and bring them down for her.
Replace probe control board and replace probe isolators. work will include removal of old control board installation of new control board. removal of probes and probe isolators installation of new probe isolators and reinstall existing probes torqued to manufacturer specifications installed with Teflon tape and anti-seize. Due to system not operating at this time checked all possible other parts that could be checked without system running once these parts are installed and system is running other parts can be tested to check for proper operation due to system not operating at this time cannot determine if there is any other problems ( other problems may exist )Installed new parts tested operation of system found system operating with no other failures at this time reset high limit and operation limit controls to manufacture specifications.
Eight-year-old Bradford white water heater located in an exterior closet had its pilot light go out again, homeowner has mentioned it does happen fairly frequently due to its location the wind gusts through that area specifically. I relit the water heater found no fault codes everything seems to be operating properly but did recommend quite a few repairs on it. Also inspected the secondary water heater that unit is from 1998
Performed furnace diagnostic Roseville, found zoned rheem system not working correctly downstairs has no air flow. Found zone damper spring broke. Grabbed spring and stretched it, the. Re attached it tested vents, working now.
Install 4 Ton American Standard 17 SEER / 13 EER Two Stage Compressor / 80% Up flow Two stage furnace with Variable Speed Blower. New electrical whip and electrical disconnect, new gas flex,new condenser pad, nitrogen line set flush and then charge system to manufacture requirements with R410a Refrigerant. Replace Zone board with Honeywell zone board 3 WiFi thermostats, Duct seal and perform Title 24 duct test and job will require permits to be pulled.
Watts 1/2 inch model 009 regulator has failed its blasting out water will replace with new 009 model 1 year warranty parts and labor. Installed new valve tested no leaks
Performed annual heating maintenance Roseville. 18 yr York diamond 80 furnace attic. Evidence of rodents in attic see pictures. Found kinked duct right at hatch. Also filter dirty. Recommend washable filter due to size of filter. Blower motor and capacitor have been changed blower capacitor email@example.com ok. Hot surface ignitor ok. Board looks ok for now. No burnt marks. Cleaned burners and flame sensor. Found burnt insulation in burner compartment .System has been worked on in the past. Would recommend washable filter. Then we can think about clearing and cleaning platform. And un kinking those ducts.
Performed annual heating maintenance on a 4 yr old Lennox split system. Tested system system turned right on. Change Filter 20-30-1. No evidence of anything in attic no rodents at this time checked equipment. Cleaned burners and flame sensor. Checked gas pressure. Electrical connections tight no burnt or loose wires. Control board ok. Blower is clean. Ducts are silver flex ducts sealed well. High efficiency furnace draining well at this time, tested system safety features working at this time. Checked drain to ensure proper drainage. Secondary drain pan look good.Put the system back into ac mode at 78 degreesOnly new recommendations, unit surge protection. And upgraded filtration to keep the system clean for as long as possible. Dust levels can be reduced with upgraded filtration adding an air scrubber plus can clean home and remove dust.
Customer has leaking airgap, removed hose and cleaned and added 90 degree copper to take the proper turn. Test with no leaks.
Performed furnace tune up on a 8 yr old Lennox gas package unit ground. Found system in not the best shape. No drain line causing water to not drain correctly and rust system. Need to add drain line. Found burner compartment full of spider webs. Cleaned burners and flame sensor. Removed webs, checked blower motor variable speed. Checked ac coil, found some oil stains, talked to clients daughter she mentioned the system froze up before. Need to keep an eye on refrigerant levels next visit. Filters in house just changed all 3 of them. Checked gas pressure. Silver flex ducts under the house. Test ran system cycling on its own. Working at this time.Recommend the annual maintenance to check everything out. Also fixing the drain lineInstalled primary drain line with trap and clean out, and routed it to the dirt next to unit. See pictures
Hot side supply line is leaking due to damage during install will replace and test.no leak tested good .hvac equipment all original provideding membership
Performed furnace maintenance on a 29 yr old Goodman dedicated horizontal Roseville. System not in the best shape. Ac coil in attic leaked damaging the ceiling. Coil pan very small barely covers coil. Ducts grey with duct tape starting to fall off. Brushed off debris from unit. Lots of sawdust on platform and unit. The unit has been maintained or repaired in the past, it has a newer ignition control module. Washed filter. Cycled system on, since itâ€™s a natural draft furnace it takes a long time to ignite. System is running due to its age itâ€™s just not as efficient as it couldInspected furnace for safe operation, Found failure in heat exchanger compartment. Informed client showed pictures and emailed pictures as well, client signed that he is aware and is going to run system at his own risk. No co in present in home at this time.
Customer was not getting hot water in her shower, upon diagnosis the water heater is working but her recirculation pump needed adjusting. Further diagnosis revealed soot marks on the front of the water heater which points to exhaust escaping the front of the unit which is a danger. The water heater is original to the home and has a date of 1992 on it give or take a couple years and needs to be replaced. I left multiple estimates to replace the water heater and recirculation pump and the customer will contact us when they decide what they want to do.
Found steam room boiler not functioning inspected system found problem is with probe control board. called tech-support due to issues with unit prob control board controls control boards in unit. unit should not have been operating at all tested system and found it to be caused by control board feeding voltage through but when high amp is pulled meaning multiple devices calling for power it is not able to supply power as needed. inspected probes found probes to be clean, inspected probe isolators completely full of calcium not draining water, inspected bottom of tank can visually see calcium buildup debris at bottom of tank almost as high as heating elements. recommend full system maintenance due to age of system being over 10 years old. recommend quarterly maintenance to be performed to inspect and check proper operation of system this will correspond with manufactures recommendation with the age of the system it is highly recommended to catch a small problem before it turns big th
Made correction repairs
We will remove old equipment and dispose per E.P.A. Regulations and install the 16 SEER equipment that is listed above. Installation will include, new drain pan with risers, new pig tail and we will install a new return to maximize airflow returning to the system and allow system to run at its full potential. New return plenum needed to accommodate the current and new return. Replace current 20â€ return with new 20â€ return duct. Remove Smartvent from system. Outdoor condenser will have all new electrical disconnect with whip. We will cut off bad union that is kinked and replace with new union and line set. Insulate new line set to wall. New condenser pad. Line set will have a nitrogen purge to clean out any contamination and will be vacuumed down to ensure that there is no leaks. System will then be charged to manufacture requirements with R-410a Refrigerant.. System will be run tested on all operating functions. Nest thermostat will installed as well. We will pull permits and h